When you need air conditioning, heating and water heater services in Berwyn, PA, you need DiBiase Heating & Cooling Company. We’ve earned a reputation over the years for providing customer-first service you can count on.
We live by rock-solid values of integrity, honesty and quality. Read our reviews and find out why your neighbors think of our trusty frog mascot whenever they need local heating, air conditioning and water heater services in Berwyn, PA.
for Berwyn, PA
Our Reviews by City
Service call that the Air Handler in the Attic was dripping water into the Condensation Pan. Upon arrival spoke with homeowners and found water damage on their living room ceiling. Proceeded to the Attic to inspect system. Found unit was pitched slightly to the back of the unit causing water to leak out the back. Pitched unit towards the Drain Pan. After issasembling the Unit, found the Primary Drain Pan for the Coil was extremely rusted and water was leaking through. Due to the Age of the system 5/1992, recommend replacement of the entire system. Unit will continue to leak into the Auxilary Drain Pan if it is in operation.The office will call and schedule a time for Joe to come out for an Estimate.
Performed Precision Air Conditioning Tune Up on the First Floor and Second Floor System. Replaced both High Efficiency 413 Air Filters. Cleaned EZ Trap and Drain Line for the Second Floor System. Tested Electrical Components on the Indoor and Outdoor Units. Measured Refrigerant Levels of each system. Both systems are running to standards.
Replaced thermostat on a carrier Package roof top unit.
Installing a 3-Ton Amana Gas Furnace and Air Conditioner in Berwyn. This home home has two units which separately control the Air Quality for the First Floor and Second Floor. Last week we installed a new system for the Second Floor. This installation today is for the First Floor Unit. Some Air Quality features with this install are a Reme Halo Air Purifier and a Humidifier.