When it comes to your Bryn Mawr, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Bryn Mawr, PA to see how we live up to these values every day, in every way.
for Bryn Mawr, PA
Our Reviews by City
Performed Precision Air Conditioning Tune Up on the Air Handler and two Condensing Units. Replaced both Air Filters. Attempted to take apart the Condensation Drain, but was unable to take apart and clean. Cleaned Drain Line and Discharge Tubing. Recommend replacement of the Condensation Pump to a newer style that is more accessible so that it can be cleaned properly. Checked Tension and condition of the Blower Wheel Belt.While testing the Refrigerant Levels of system, found the Right Outdoor Unit system was not running at the correct Refrigerant Pressures. On a previous Tune Up, the TXV had been diagnosed with a restriction. Recommend replacement of the TXV and rechecking the Refrigerant on the system. The 5 Mfd Capacitor for the Right Outdoor Unit was testing below Rating. Recommend replacement of the Capacitor. Included estimate for all recommended repairs.Due to the restriction on the Right TXV, the system is only producing about a 15 Degree Temperature Split between Supply an
Performed Precision Air Conditioning Tune Up on system. Checked Air Filter. Cleaned Condensation Drain Pipe. While testing system, found unit to be low on refrigerant. System was only producing a 10 Degree Temperature Split between supply and Return. Added R-22 Refrigerant to system to increase temperature split and balance the pressures and temperatures of the system to recommended levels.Will follow up with additional information/pricing about installing a Pressure Switch into the system to allow th Air Conditioner to run during cooler ambient temperatures. Also recommend installation of an EZ Trap onto the Drain Line. The EZ Trap would be wired into the system, and shut the unit down if it ever became clogged.Homeowner signed up for Service Membership. Only wants the the Air Conditioner serviced. Next Spring/Summer when we return for the AC Tune Up it will be the second visit on the Membership Plan. Today was the First Tune Up on the Membership.
Performed Precision Air Conditioning Tune Up. Changed filter, customer supplied. Informed customer to make attempts to change out filters every 2-3 months as the last one was very dirty and clogged. This will help with the efficiency with air flow and cooling of home during summer. System is running at operational standards.Checked dehumidifier, washed filter, and checked condensate pump. The Unit is operating at manufacturer specification. Unit is set to 53% Relative Humidity.Informed customer on operation of dehumidifier. When customer adjusts the level of relative humidity on the unit, it will perform â€œAir samplingâ€ mode in which it will pull in current relative humidity (RH) level of the basement and compare it to user setting. If the current RH of basement is higher than setting, the unit will then kick into â€œdehumidifyingâ€ mode until it reaches 3% RH below setting and shuts off. If RH of basement is below settings, the unit will not perform sampling mode. The unit d
This is not a good day for the pumpkin! Don’t have a bad day in the middle of winter like the pumpkin is having today. When we perform a Tune Up on your Heater, we help make sure that doesn’t happen.