DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Chadds Ford, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Chadds Ford, PA.
for Chadds Ford, PA
Our Reviews by City
Performed Precision Air Conditioning Tune Ups on the 4 Central Air Systems and the 3 Ductless Split Systems. Replaced the 3 High Efficiency 213 Air Filters and the 16x25x1 Air Filter. Cleaned the Air Filters and Indoor Coils on all the Indoor Ductless Systems. Checked Electrical Components on the Indoor and Outdoor Units for all Systems. Cleaned all Drain Lines and Condensation Pumps. Filled Condensation Pumps and tested to ensure they were pumping properly. Turned Humidifier Dampers to the Closed Position and turned off the Humidistat Controls for the Season. Measured Refrigerant Charge on all systems. Due to Ductless Systems having a Critical Charge the refirgerant Charge was not measured. Found the two systems for the Main part of the 1st Floor of the House were slightly low on refrigerant. Subcooling was 3 Degrees or below for both Systems. Added 2 lbs of 410-A to each system, Charging by subcooling. Subcooling was raised to recommended levels after adjusting Refrigerant. All syste
Performed Precision Air Conditioning Tune Up on system. Replaced 20x22x1 Air Filters. Cleaned Condensation Drain Pipe. Closed Humididifer Damper for the Air Conditioning season. Tested Refrigerant Levels using a Charging Jacket due to lower Outdoor Temperature.
Cleaning the Heat Exchanger on a High Efficiency Ulta Boiler in Chadds Ford as part of the Heat Tune Up. This home has multiple systems which along with this Propane Fired Boil, include a Rheem Propane Gas Furnace, several Trane Heat Pumps, and three Mitsubishi Mini Split systems.