DiBiase Heating & Cooling Company proudly serves our neighbors in Chester Springs, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience.
We do this by providing the fastest services from the most qualified technicians in the Chester Springs, PA area. See what your neighbors are saying about our unshakable customer-first service!
for Chester Springs, PA
Our Reviews by City
Very courteous and efficient service
Forrest - Chester Springs, PA
Great service - both from the office and from the technicians
Tilo - Chester Springs, PA
Dino - Chester Springs, PA
Positive Repair Experience
Joseph - Chester Springs, PA
I'm new customer. Found a problem my previous provider overlooked. Repair cost was reasonable. Technician was professional, competent and courteous.
Robert - Chester Springs, PA
Luis did a thorough job checking over my system as well as educating me on how it works.
Thomas - Chester Springs, PA
Chris was remarkably thorough and communicative with lots of information about options open to us. Instead of pressure to take the expensive way, he provided ideas on how to simplify and save. The service itself was excellent.
Jim - Chester Springs, PA
Great service. Technician explained everything clearly
Yang - Chester Springs, PA
Marybeth - Chester Springs, PA
Jamie - Chester Springs, PA
We have used many HVAC companies and found a true gem in DiBiasi! Professional, knowledgeable, courteous and prompt. We have used them for maintenance for nearly 4 years and just recently replaced our 12 year old system with wonderful success. Thank you DiBiasi!
Ellen - Chester Springs, PA
Chris - Chester Springs, PA
Service call on upstairs A/C
Michael - Chester Springs, PA
Excellent service. I requested an appointed to get my upstairs A/C unit checked out, suspecting that it needed a recharge. I got a call back from Steve right away saying someone could come out in the afternoon between 2 and 4. Dan and Nate arrived shortly after 2 and checked it out. They were very friendly and professional. After taking a look they said the refrigerant was low and needed a charge. They gave me a estimate for the work which I agreed to and were able to finish the work quickly. Overall a very good experience.
Cheryl - Chester Springs, PA
Nancy - Chester Springs, PA
The two guys who came were terrific representatives of your company! Excellent service and personable. They talked to me about getting a tune up for both heat and AC without making it feel like they were pressuring me to buy something. Can't say enough about them and how great they were. Oh AND they fixed my AC unit.
Chris - Chester Springs, PA
Donna - Chester Springs, PA
Experience was wonderful. Brian was great and very informative!
Ellen - Chester Springs, PA
Julie - Chester Springs, PA
Nathan and his partner from DiBiase replaced a long stretch of vinyl tubing that led from my condensate pump to my sump pump. Their work was excellent and reasonably priced. They went the extra mile by protecting the tubing with PVC pipe and anchoring it with cable ties to prevent my cat from chewing it. I was very satisfied with the job they did.
Julie - Chester Springs, PA
This was my first service call with DiBiase. The guys who came out to my house were professional and knowledgeable. Bryan answered all my questions. They used booties on their shoes and were very respectful of my home.
Rick - Chester Springs, PA
Great service, pleasant disposition
Karen - Chester Springs, PA
Knowledgeable. Pleasant. Efficient.
Responsive and informative
Tom - Chester Springs, PA
Brian and his colleague were thorough, considerate of our home, and very communicative about condition of equipment and options for servicing.
Melissa - Chester Springs, PA
Quick turnaround service for a heating emergency company was able to come out same day very professional and courteous!
HVAC Company with Reliable Service and Experienced Technicians
Denise - Chester Springs, PA
I have used DiBiase HVAC for service at my personal residence and several of my rental properties over the last year, after switching from a well-known local company who was gouging me with their prices. I have had the same service technician, Bryan Dusewicz, on multiple occasions. He is always on time, very friendly and is quick to diagnose the problem. I have found Bryan to be very trustworthy, both from a security standpoint and from a business perspective. Joe is the owner of DiBiase and seems genuinely interested in meeting client expectations. I highly recommend DiBiase for HVAC work in the Chester County area. -Denise Warfel (Chester Springs, PA)
Cut 3 in pvc exhaust stack higher and also re attached bathroom exhaust flex use pipe strap to hung flex, all connections were taped and zip tied,
removed suction valve recto seal gas Guard, and install new regular brass cap, and also install internet red link gate way to make thermostat WiFi, set up thermostat and gate way, went over settings and how to manage app from the phone customer ok
Checked condensate, read home inspector report, he stated that the inducer has water in it. Tested inducer, found no water in it started inducer, found that the bearings are failing. Need to replace inducer for first floor air furnace Need inducer for Trane model TUX100C948D2
Performed peco heat-pump check up, electric heat as back up, customer has thermostat that has no emergency heat option, replace filter 20x25x1 flushed drain test pump ok check outdoor unit 410 pressures ok capacitor, contactor needs replace, cycle unit, quoted for repairs and also new T6 WiFi thermostat
Need to work up estimates, customer has unusual set up. Mini split do 3 rooms on first floor and attic system does second floor and one room on first floor.
Installed new amana heat pump system. Installed new 16x20x1 air filter. Ran new lineset. Adapted to existing metal plenum. Installed 115 v condensate pump and vinyl hose. Pressures and leak checked system. Tested out system, system is running to manufacture specifications.
Checked bathroom exhaust, found flex is very long and trapped and the stack is at attic floor level. Need to cut stack and replace exhaust venting.Checked mini split, found poor cooling, checked refrigerant charge, found indoor eev not opening enough causing high head pressure and low suction pressure 29 subcooing and 0 superheat.Need to return with 20â€ 5â€ exhaust flex and hanging strap. Need to remove old exhaust and cut the stack higher and pitch new exhaust Need someone to look at first floor lay out and see if attic air conditioner can cool 3 rooms 2 have min splits nothing in the kitchen
Performed cooling maintenance, checked air filter, inspected cooling coil. Cleaned condensate drain and trap. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Drop off filters
Found blockage at the exhaust pipe termination outside house, quoted for repairs to clear pipe customer ok with price, cleared blockage, removed bird nest both pipes are clean now,
Performed cooling maintenance, replaced 2 standard air filters, 16x20x1, checked media filter rp413. Cleaned condensate drain and, blew out condensate traps. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioners and heat pump, checked refrigerant charge and temperature drop across coils.
Checked no cooling complaint on second floor air conditioner, checked air filter ok. Started air conditioner, checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced by superheat. Checked operation and temperature drop across coil.
New Heat Pump Installation
Performed Precision Air Conditioning Tune Up on First Floor and Second Floor Systems. Replaced all Air Filters for both Systems. Closed Damper on Humidifier and turned off at the Humidistat Control. Cleaned Drain Lines and the Condensation Pump that is with the First Floor System. The Vinyl Tubing appears to be dirty and getting debris in it. While cleaning the Pump removed Vinyl Tubing and blew through to ensure it was clear. Filled Pump and tested operation to ensure it was primping out. Checked Electrical Components on both Systems. Measured Refrigerant Charge on both Units. Both systems are running, but are doing so inefficiently. Amp Draw on each Compressor is within rating, but is slightly higher than normal. This could be attributed to the age of the Systems. The Compressors are working harder to run than usual. Do to age of the Systems, would recommend begin planning for replacement of the First Floor and Second Floor Systems.Thank you for renewing your Service Membership fo
Checked no cooling complaint, found breaker tripped, found bad dual run capacitor, also a shorted compressor on 14 year old heat pump canâ€™t read outdoor label but the unit next door is a 2 ton heat pump.Recommend replacing system due to age.
Performed cooling maintenance, found no air filter, installed 16x25x1 filter. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values, found weak blower capacitor. Replaced blower capacitor. Started air conditioner, checked refrigerant charge, found low on charge. Topped off charge.Need a quote on replacing 3 ton air conditioner
Checked no cooling on second floor air conditioner, found low on charge, topped off charge. Balanced by superheat. Checked operation and temperature drop across coil. Recommend leak search on system. See no oil or obvious leaks. Need to schedule leak search.
Performed Six Month Inspection on Second Floor Amana System that was Installed in 1/2019. Checked Air 16x20x1 Air Filter. Filter was clean and did not need to be changed. Cleaned EZ Trap and poured Water Through Drain Line to Test. Put system in AC Mode and measured Refrigerant Charge. No additional charge was needed beyond what was added during installation. System is operating to standards at this time. As per the Home Inspection Report the Door Switch for the Blower Compartment was not working properly. Found Switch was getting stuck due to something that was stuck in the Switch. Removed small piece of plastic which allowed the switch to open and close properly. Tested operation of Door Switch.Performed AC Tune Up on First Floor System. Replaced the 16x20x1 Air Filter. Inspected Electrical Components on Indoor and Outdoor Units. Found the Dual Capacitor on the Outdoor Unit is working but is rusted. Also found Contactor working but Terminals are starting to rust and the Coil is be
Performed two ac check ups, check electrical low and high ok check filters ok, we will return to install new filters, check split ok flushed drain test and clean pumps, second floor pump ok, noticed first floor pump taking too long to discharge, replacing vinyl tubing for both units and also replacing pump for first floor unit, check outdoor units 410 pressures contactor and capacitors ok super heat and sub cooling ok customer will take care of pump and discharge vinyl
Performed cooling maintenance on 3.5 ton air conditioner, replaced standard air filter, cleaned condensate drain and pump. Inspected cooling coil. Checked voltage, amperage and electrical connections. Measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Checked no cooling complaint, filters are clean. Started air conditioner, air conditioner started and runs. Checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced charg by superheat. Checked operation ok.
When I arrived foundfound r22 pressures to be 213/61 and super heat is 32 and subcooling of 11 very good. Outdoor air temp is 83 degrees and discharge air temp is 98 degrees. A/c is running well outside. Went inside to indoor unit in attic and checked tempature split. Return temp was 79 degrees and supply temp was 63 degrees. 16 degree split . Ac is working fine but system is getting older and should consider replacement.
Performed precision ac tune up on Rudd ac. Replaced 16x25x1 air filter. Blew out condensate drain and cleaned out pump. Found old style ez trap on drain recommended replacing with new style ez trap with safety float. Installed new ez trap. Also checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at this time.
Checked no Heat complaint, found inducer lock rotor. Pulled inducer found a bird in the impeller. Removed bird. Installed inducer started gas furnace and checked operation ok. Signed up a membership for 2 gas furnaces and 2 air conditioners. Need to schedule cooling put.
Performed Precision AC Tune Up on Rheem System. Replaced 20x25x1 Air Filter. Air Filter was very dirty and blocking Air Flow. Cleaned EZ Trap and Condensation Pump. Filled Pump and tested operation. Inspected Electrical Components on Indoor and Outdoor Units. Found the Dual Capacitor on the Outdoor Unit was testing below rating on the Compressor Side. Installed a new 50/5 Mfd Dual Capacitor and tested operation. Measured Refrigerant Charge on system. Refrigerant levels are within standards at this time. Refrigerant was added to System last year. Outdoor Unit and Furnace are Rheem and the Indoor Evaporator Coil is a Trane. System is about 14 Years old. Due to age and efficiency of system, would recommend begin planning/saving for replacement of the Gas Furnace/AC System.