DiBiase Heating & Cooling Company proudly serves our neighbors in Chester Springs, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience.
We do this by providing the fastest services from the most qualified technicians in the Chester Springs, PA area. See what your neighbors are saying about our unshakable customer-first service!
for Chester Springs, PA
Our Reviews by City
Competent and Professional Follow-up Service
Joseph - Chester Springs, PA
This was a follow-up check on a potential refrigerant leak. A very slow leak was discovered. Kurt showed me where the fluorescent dye was showing on an indoor coil. He then measured the system pressures and found that almost no refrigerant was lost during the 1 month elapsed period. Kurt discussed all the repair or replace options and answered my questions. I decided on a "wait and see" strategy for now. Very satisfied with how this service problem was handled. Five stars.
Furnace and air conditioning installation
Samantha - Chester Springs, PA
Michael - Chester Springs, PA
I had an annual checkup for my gas furnaces. The guys were very polite and professional. Luis explained everything they did and answered all my questions. Very happy with the service.
Great Service and good price point!
Greg - Chester Springs, PA
Kurt was great...very professional
Roger - Chester Springs, PA
Kurt was great...very professional
Dino - Chester Springs, PA
friendly and professional
Great service plus an education.
Joseph - Chester Springs, PA
My problem: Heat pump gradually stopped cooling over a period af about 1 month.Service diagnosis: Very slow refrigerant leak.What was done: Refrigerant was added to immediatly restore normal operation along with a fluorecent dye to enable inspection and location of the leak at a later time.Education: Learned that as the AC cools the air it dehumidifies. (I knew this) What I didn't know was that the dehumidification is the reverse of evaporation. Evaporation cools the air. Dehumidification heats the air the same amount as the air was cooled on evaporation. So this heating effect fights the AC trying to cool until the humidity is removed. Then the temperature starts to drop. This effect is most noticeable after the AC has been off for a long time and the house is hot and humid.
Inezn - Chester Springs, PA
Texts were very friendly, helpful and professional.
Great service, awesome price
Delfi - Chester Springs, PA
P family - Chester Springs, PA
Great work as always. Honest expert recommendations, respectful of our home, efficient service. We are very satisfied!
Jai - Chester Springs, PA
Great service at reasonable price.
Jai - Chester Springs, PA
Very professional and qualified technicians!
Fantastic Service, Responsive, Right Price
Chris - Chester Springs, PA
These guys do a great job!
Great Service! Thank you
Emi - Chester Springs, PA
Kurt arrived on time and was super friendly. He was thorough and worked quickly. I’m very pleased.
Prompt and efficient service
Leon - Chester Springs, PA
Excellent experience. Would use again for future jobs
Very courteous and efficient service
Forrest - Chester Springs, PA
Great service - both from the office and from the technicians
Tilo - Chester Springs, PA
Dino - Chester Springs, PA
Positive Repair Experience
Joseph - Chester Springs, PA
I'm new customer. Found a problem my previous provider overlooked. Repair cost was reasonable. Technician was professional, competent and courteous.
Robert - Chester Springs, PA
Luis did a thorough job checking over my system as well as educating me on how it works.
Thomas - Chester Springs, PA
Chris was remarkably thorough and communicative with lots of information about options open to us. Instead of pressure to take the expensive way, he provided ideas on how to simplify and save. The service itself was excellent.
Jim - Chester Springs, PA
Great service. Technician explained everything clearly
Yang - Chester Springs, PA
Marybeth - Chester Springs, PA
Jamie - Chester Springs, PA
We have used many HVAC companies and found a true gem in DiBiasi! Professional, knowledgeable, courteous and prompt. We have used them for maintenance for nearly 4 years and just recently replaced our 12 year old system with wonderful success. Thank you DiBiasi!
Reclaimed and removed old equipment. Installed new coil, condenser, and furnace. Brazed with nitrogen and pressure tested. Reconnected everything to furnace and tested system. System operating fine at time of install. Will come back to reconnect humidifier and adjust refrigerant charge.
Service call that the Heat was not running. Found system turned off upon arrival. Turned system on to test operation. Inducer Motor was running and the Flame Sensor was lighting but the pressure switch was not closing long enough to allow the system to fire. Inspected Tubing and found water collecting in the tubing. The Tubing was too long and was drooping causing water from the Secondary Heat Exchanger to buildup and not allow the pressure switch to close. Cleaned tubing and shortened the tubing. Exercised pressure switches and cleaned drain lines off the furnace. The Blower Capacitor was testing below rating. Installed a new 20 Mfd Blower Capacitor and tested system. Performed Combustion Analysis while measuring Gas Pressure.System is operating but is overall in poor condition. There is excessive rust damage inside and outside of the Furnace. The Inducer Motor is operating, but the internal bearings are beginning to wear causing the motor to run louder.Also would recommend perf
Performed two gas heater check ups, check electrical low and high filters ok clean sensor and check burners ok gas pressure ok combustion test cycle both heaters ok check split test pump for first floor ok, also service humidifier for first floor unit set to winter 35%
Performed gas heat tune up. Cleaned flame sensor. Replaced air filter. Checked gas pressure. Checked for gas leaks. Tested capacitor. Inspected electrical connections and components. Checked temperature rise. Performed a combustion test. System operating as it should at time of service. Looked at water heater and found heavy rust and corrosion on joints. See picture. Showed customer and advised on repair. Will let us know.
First floor Performed heat tune up. Checked temperature rise. Checked gas pressures. Checked combustion. Measured capacitor. Inspected all electrical connections and components. Cleaned flame sensor. Replaced air filter. Noticed some bearing noise from inducer motor. Checked for gas leaks. System running well at time of service.Second floor Performed heat tune up. Checked temperature rise. Checked gas pressures. Checked combustion. Measured capacitor. Inspected all electrical connections and components. Cleaned flame sensor. Replaced air filters. Checked for gas leaks. System running well at time of service.
Performed gas heat tune up, check electrical low And high ok clean sensor and check burners ok, replace filter, gas pressure ok during combustion test found flue temperature very hot over 160 gas pressure ok inducer was replaced 2014, check orifice does not have yellow orifice, would recommend installing the orifice, cycle heater ok would recommend replacing heater due to previous experience with same units
Performed precision heat tune on amana gas furnace, checked flame sensors and electrical connections blew out drains, adjusted gas pressures to factory standards and then performed combustion analysis checked out good. Changed air filter checked temperature rise.
Checked 410a pressures at 70 degrees outside temp in a/c mode. Pressures were 264/123 with a subcooling of 6.8 not terrible at this time. Used flash light and glasses and looked over indoor and outdoor coil. Found some dye at indoor evaporator coil in very back top corner. Evaporator coil is leaking. Homeowner is going to let system go at this point till charge gets low again. Heat pump system is about 10 years donâ€™t recommend repairing.
Performed Quality Assurance on Amana Gas Furnace/AC system. Completed Checklist Form in system. Corrected any issues found. Reviewed installation with Homeowner.
Performed heating maintenance, checked media filter ok. Started humidifier, checked operation. Serviced furnace, cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test, checked operation and temperature rise.
Performed four heat tune ups, two propane heaters, one heat pump with 20 kw back up and a duct less heat pump, check electrical low and high ok replace standard filter 413 ok for heat pump cleaned filter for mini split, clean sensor and check burners gas pressures combustion test cycle both heaters ok service humidifier for first floor unit and test ok check outdoor pressures for heat pump test 410 ok, on mini-split check split ok supply 130 rerun 74
Installed a new gas furnace on return box with a new coil and new linesets and thermostat wire for outdoor unit. New condensate pump and ez trap both wired into r for saftey to shut off thermostat. Unit was triple evacuated and pumped down to 238 microns and holding for ten minute Unit was also pressure tested for 10 minutes at 352 psi and held. Condensate pump was installed with 2 cork pads to elevate off ground a new outlet and switch with 4x4 box was installed and unions on both furnace drain and ac drains. The venting was re connected and a water protection drain coupler installed on intake for cabinet protection unit was tested in ac and heat and meet manufacturing specifications. 16x25x1 air filter installed with bracket.
Installed new furnace in existing location on cork vibration isolation pads. Installed new Aprilaire 2410 air cleaner. Installed new 10x25 return air drop from trunk. Converted furnace to propane. Completed supply and return duct connections and sealed. Installed new coil on furnace and installed new EZ trap and wired to shut down system. Reconnected single 3" vent exhaust pipe and reconnected gas line. Installed new switch and outlet. Replaced condensate pump and vinyl tubing to the point of discharge. Installed Reme air scrubber. Reused existing Ecobee 4 thermostat. Installed new Aprilaire 600M humidifier and wired to be controlled from Ecobee 4 thermostat. Installed new outdoor unit on new pad and pump up legs and leveled. Installed new disconnect box and whip with surge protector to unit and sealed disconnect to wall. Installed new copper line set from indoor coil to outdoor unit with tear resistant line set. Pressure tested, evacuated, and charged and tested system. Setup Para
Performed heating maintenance, checked media air filter ok. Serviced humidifier, cleaned and replaced water panel. Started for winter. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, performed combustion test. Checked operation and temperature rise.
Performed two gas heat check ups, check electrical low and high ok check burners and gas pressures adjust gas from 3.9 to 3.44 inches water column also clean sensor, test pump and check split ok, replace filters and combustion test ok cycle both furnaces ok, both furnaces are working ok at this time,
Performed heating maintenance, replaced standard air filter. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
Performed heat check up, gas furnace check electrical low and high check filter, clean sensor, and check burners ok, gas pressure set to 3.5 wc combustion test ok check split ok also test pump cycle furnace ok inspect exchanger customer seen exchanger condition recommended having blower clean customer wants to wait at this moment... emailed quote
Replace high efficiency filter for air cleaner 413
Performed oil heat tune up, on boiler, clean exchanger and chimney base, replace nozzle 1x80B and Also replace electrodes, clean cad cell eye and check transformer ok,, check boiler operation pump strainer and oil filter ok performed smoke test ok combustion test ok check humidifier operation for first floor unit,,,set to 35% check hot water coils working ok, also check reversing valve operation,
Performed gas heat tune up check electrical low and high ok clean sensor and burners ok replce high efficiency filter 423....check gas pressures combustion test ok check split cycle furnace ok furnace is in good working order, supply temp 126 return 78
Performed precision heat tune up on Rudd gas furnace. Replaced 20x25x1 air filter. Also serviced Aprilaire humidifier replaced pad. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Cleaned flame sensor and blew out all tubing. Tested operation of pump. Rudd gas furnace is working fine at time of service.
Performed precision heat tune up on oil furnace with Lennox heat pump. Checked model 2200 air filter is clean. Replaced.85x60b nozzle. Homeowner wants to replace garber oil filter next tune up. Performed combustion test. Checked operation of heat pump in heating mode. Checked operation of oil furnace in emergency heat mode. Checked temperature rise. System is working fine at time of service.
Performed Quality Assurance On Amana AC/Gas Furnace System. Replaced 20x20x4 Air Filter. Reviewed installation with homeowner. Completed Checklist Form in System.
Performed heating maintenance, checked media air filter. Cleaned flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, measured fuel pressures. Performed combustion test. Checked operation and temperature rise
Performed heating maintenance, checked media filter, need to replace Rp 413. Cleaned flame sensor, inspected heat exchanger. Checked furnace setup. Checked voltage, amperage and electrical connections. Started gas furnace, measured fuel pressures. Performed combustion test. Checked operation and temperature rise.Need rp 413 did not have at time of maintenance