DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Coatesville, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Coatesville, PA.
for Coatesville, PA
Our Reviews by City
Compotent professional and pleasant.
Stephen - Coatesville, PA
Great job all around!!!
Dawn - Coatesville, PA
Great Freindly service
Jerzy - Coatesville, PA
Showed up within a half hour of me calling and my heat was fixed in no time. They did a great job.
Justin - Coatesville, PA
Pleasant and informative-shows concern for his customers
Richard - Coatesville, PA
Jayne - Coatesville, PA
Technician was wonderful. Thorough and explained everything well.
David - Coatesville, PA
Beth - Coatesville, PA
Repair man courteous, knowledgeable, explained everything to me so I could understand. You have my business in the future.
Good service .. very ptofessional
Sue - Coatesville, PA
A fabulous company
Joan - Coatesville, PA
I have used this company 11 years. They are extremely knowledgeable, they explain everything to the customer. Always on time, have technicians in uniform in a marked truck. All work is always done professionally and competently. I would recommend to anyone!
Duamell - Coatesville, PA
Very happy with the repair. Hoping it lasts and I won't have a leak again.
Gail - Coatesville, PA
Great Service. Nice people
LuAnn - Coatesville, PA
We love Nat. We does a great job. He is on time and meticulous.
They are more interested in fixing the problem then just trying to sell you something
Andrew - Coatesville, PA
David - Coatesville, PA
DIBIASE does it right! After making the appointment it was confirmed, I received a reminder, on the day of the appointment I received an email with a picture of the gentleman who would be doing my tune up. Nate could not have been more friendly, polite, or professional.
Sue - Coatesville, PA
Excellent service. Nathan is very diligent and an asset to your company
Great service – pleasant efficient employee you have in Nate
Richard - Coatesville, PA
Great service – pleasant and Knowledgable employee Nate
Ted - Coatesville, PA
Follow up call to check on water heater installed 3 months ago. Replaced fitting with history of failure at no charge.
Good price, knowledgable and helpful staff
Lisa - Coatesville, PA
I was able to schedule the job quickly and communication with Joe was great. He responded too my questions in a timely manner and answered all questions throughly. Technicians arrived on time, were knowledgable and communicated as needed.
Stephen - Coatesville, PA
I made the right decision to contract with DiBiase
Excellent service because of well-trained employee
Richard - Coatesville, PA
Concise evaluation of heating system
Kerry - Coatesville, PA
Like always - complete pros - did great work
Amy - Coatesville, PA
Marcus - Coatesville, PA
Bryan came out before my scheduled time which was great. He found the issue right away. Explained everything to me and gave me a quote before performing repairs. While fixing one issue he brought my attention to another issue....not looking for more business just making me a more aware customer. I thought that was great. Again gave me a quote with "No Pressure" to have the work done right then. I will strongly consider them again for future issue. Thanks Bryan!!
Warren - Coatesville, PA
Friendly tech and very knowledgeable
Upon arrival we noticed the fan was just running without the outdoor kicking on pressures were ok checked filter and noticed it was bad error code flashing on outdoor high pressure lock out. Which is why unit was running in auxiliary heat. Need to replace filter 16x20x1. Went back the same day and replaced the filter.
Replaced gas water heater shut off valve and put it a new shut off valve for the humidifier, during work process noticed the exhaust was leaking from vent piping told customer about leak and he instructed us to fix leak cut out old pipe added new vent
Repair leak at 3 in exhaust pipe, due to condensation leaking, on one of the joints, prime and glued necessary joints make sure no leaks were present after repairs ok, also clean and seal line set on coil termination, insulated with heat tape, also insulate exterior txv, to prevent condensation test heater cycle ok test pump ok noticed water heater is from 2000..... 19 years old highly recommended replacing water heater
Performed quality assurance inspection on steam boiler installation. Boiler has been working good and maintaining temperatures even on coldest days. Water level holding steady. Installation looks good.
Performed Precision Heating Tune Up on Gas Fired Carrier Furnace. Replaced 16x25x1 Air Filter. Cleaned and serviced Aprilaire Humidifier. Tested operation of Humidifier. Set Humidistat Control to level 5. Cleaned Drain Lines for Furnace and tested Electrical Components. Found the Blower Motor Capacitor was testing below rating. Installed a new 10 Mfd Blower Motor Capacitor and tested operation. Performed Combustion Analysis on Furnace. The Intake and Exhaust Pipes are ran with both PVC Vent Pipes and ABS Pipes. Would recommend replacing the sections of the Vent Pipes that are ABS Pipe with PVC Vent Pipes.Homeowner informed me that Saturday the Furnace stopped running and then began to work again after several attempts at turning power on/off. During Tune-Up the Furnace was working properly with no issues. If issue occurs again, please leave System in that state until we come out to diagnose.Also spoke about the Air Scrubber to help enhance Air Quality in the Home. Please see attac
Performed precision heat tune on natural gas rheem furnace. Checked all electrical conections , tested condensate pump operation, cleaned out drain tubing, and performed combustion test, all in proper working order at time of service..
Performed quality assurance on new boiler and water heater installation. All looks good.
Replace Water Heater and checked for leaks
Performed gas heat inspection check electrical low and high ok clean sensor and burners ok gas pressure ok combustion test ok replace filter check split ok cycle furnace ok test pump ok supply 120 return 65 recommended replacing filter every 30 days,,,,,
Drained the water heater and hooked new up inside pan with alarm on bricksnew exhaust and copper from tank to valves also new expansion tank in. Tested water and alarm all working great
Removed and installed steam boiler. Reconnected steam supply and wet return to steam boiler . Redid Hartford loop for return so boiler would not flood . Reconnected gas , high and low voltage wiring and exhaust vent to chimney. Installed a auto fill for boiler and connected to low water cut out . Water fill is set up so when low water cut out hits the lwc will fill the boiler till satisfied. Installed new T6 thermostat. Filled boiler to water level and tested . Boiler ran and steam supply and wet return were hot . Boiler did not over fill or over pressure. Tested every radiator and made sure they heated up . House temperature when first tested was 48 , house temperature before we left was 65. Cycled thermostat for proper operations. Tested overall system and system is running to standards.
Performed gas heat tune up, check electrical low and high clean flame sensor and burners ok gas pressure ok replce folter 16x20x1 check and clear all drain tubing, check temperature split ok. Combustion test cycle heater ok recommend replacing air filter monthly
Performed precision heat pump tune up. Tightened and checked all electrical components and connections. Checked refrigerant pressures and tested operation. Return temp was 66 degrees,and supply temp was 88 , 22 degree temp rise.
Loud Vibration from blower, Tenant thinks is from blower, inspect and check blower wheel and motor ok, he was telling me that when he touches return panduit return chase base, stops, renforce sheeet metal with screws and piece of drive across bay, also needs new filters special size 10x20x1
Performed gas heat tune up, check electrical low and high ok clean flame sensor and burners ok gas pressure ok combustion test ok cycle heater new air filter and check split ok, cycle heater and test pump ok
When I arrived found Goodman heat pump a block of ice.Talked to homeowner about having to return after unit thaws out to check charge levels . Performed precision tune up on air handler only.Also put system into emergency heat only till we can return after heat pump thaws out.The customers peco account number is 78813-58011 finished heat pump check up on outdoor unit, added 410 refrigenat and also dye to system, customer ok with pricing, contactor and cap ok test defrost ok cycle heat pump ok
Removed old oil boiler and oil tank . Installed new high efficiency gas boiler with new piping. Installed new zone valves , air scoop , expansion tank and three new circulate pumps . Installed new zone panel to control each zone probably. Installed three new thermostats for each zone . Installed new indirect fire water heater . Installed piping from boiler to water heater . Reconnected hot and cold supply to new water heater . Installed new exhaust and intake vents for boiler . Installed gas from new gas meter to new boiler . Installed a tee for future gas stove . Installed new condensate pump for boiler and piped the discharge into the sink on the other side of the basement . Setup and tested overall system and system is running to standards.
Found that furnace was locked out on a code 7 ignition lock out due to re tries . Had 26.91 volts going to gas valve but not opening. Called johnstone for price and availability, they had valve so ran over and picked up gas valve and replaced. While replacing valve also noticed that wind was rushing down the vent pipes and told homeowner that during these high winds pressure switches can be affected until winds would come down and shut down furnace and would need to try an reset . Also tested for leaks and gas pressures on gas valve I had 8.2 w.c. Coming in and 3.6 w.c. Coming out , furnace back up in operation again.
Performed Precision Heating Tune Up on Goodman Gas Fired Furnace. Replaced 16x20x1 Air Filter. Inspected Electrical Components on Furnace. Cleaned Furnace Drain Lines and Condensation Pump. Removed and Cleaned Flame Sensor. Inspected Burners and Heat Exchanger. Performed Combustion Analysis on Furnace while measuring Supply and Return Air Temperatures. System is running to standards at this time.
Check boiler, flue pipe/chimney base and flue, and gas piping caped one gas line that had no valve, and pressured gas line to 5psi system looks like it is holding, but peco would come out and see if pressure is holding, with boiler condition it is in poor shape, old gas valves, burners all rusted controls also outdated, gas valve and limit, system has no water pressure some baseboard are disconnected, would recommend replacing boiler and chimney is a must do thing, needs to get inspected and repair before installing new boiler
Upon arrival we noticed water leaking from the glass on the bottom of the site glass was also completely full had to drain water from system.. also noticed water leaking from inside boiler and down the back side into the pilot... causing the pilot to go out. Informed customer about the problem recommend replacing the boiler. Joe will be out between 4-6 pm to go over options with customer.
Boiler not working, upon arrival found power off to boiler, found flue pipe not connected all the way into chimney base, 2 feet of 6 in flue pipe needed, and also chimney has a blockage chi,hey guy was here at the same time as us, found unit not connected to thermostat, canâ€™t see where thermostat wire coming into boiler there couple set of 14 gage wire that donâ€™t get connected to anything further troubleshooting need to find thermostat wire and wire into boiler, looks like boiler has not being tested start up needed check gas pressure and combustion test, expansion tank might be in the wrong side of piping will check with Joe about that,
Performed precision tune up on gas furnace.During tune up went over all major components,replaced air filter 16x25x1 .Performed combustion analysis to determine how well furnace is functioning at this time and also found slight amount of rust in heat exchanger but nothing to be alarmed about at time of service.Went through complete check list and all has passed at time of service.
Service call that the Heat Pump for the Bedroom was not working. Upon arrival, spoke with Homeowner about issue. System was calling for Heat but the Compressor was not running, and the Outdoor Fan was spinning very slowly. Opened the Control Panel and found that a mouse had come blown the Capacitor, and the wiring for the Capacitor and surrounding Wiring had melted and fused together. Turned Power off to System and removed all the failed wiring and connections. Made new wiring connections where possible and rewired if the Wiring was beyond repair. Inspected surrounding Wiring in the Control Area for Quality. Installed a new 40/7.5 Mfd Capacitor. Turned Power back on to System and tested operation. Monitored operation of system in Heat Mode. Forced system into Defrost to ensure that the Defrost Control Board and the Fan Relay were working properly. System is in operation, but overall condition is poor. Recommendation is to begin planning for replacement of system.
Performed tune up on amana natural gas furnace, replaced Aprilaire model # 413 air filter and performed combustion test on furnace. Noticed that natural draft gas water heater was over 10 years old and recommended replacement.