DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Coatesville, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Coatesville, PA.
for Coatesville, PA
Our Reviews by City
Stephen - Coatesville, PA
Consistently Good Service
Crystal - Coatesville, PA
This company is very easy to use. They update you when their technician is near. They stick to the appointment time. Their technicians are competent and don’t try to upsell you.
Linda - Coatesville, PA
On time and very courteous!
Satisfied Customer - Coatesville, PA
1st time service
Customer in Coatesville, Pa - Coatesville, PA
luis great service technition
Beth - Coatesville, PA
Compotent professional and pleasant.
Stephen - Coatesville, PA
Great job all around!!!
Dawn - Coatesville, PA
Great Freindly service
Jerzy - Coatesville, PA
Showed up within a half hour of me calling and my heat was fixed in no time. They did a great job.
Justin - Coatesville, PA
Pleasant and informative-shows concern for his customers
Richard - Coatesville, PA
Jayne - Coatesville, PA
Technician was wonderful. Thorough and explained everything well.
David - Coatesville, PA
Beth - Coatesville, PA
Repair man courteous, knowledgeable, explained everything to me so I could understand. You have my business in the future.
Good service .. very ptofessional
Sue - Coatesville, PA
A fabulous company
Joan - Coatesville, PA
I have used this company 11 years. They are extremely knowledgeable, they explain everything to the customer. Always on time, have technicians in uniform in a marked truck. All work is always done professionally and competently. I would recommend to anyone!
Duamell - Coatesville, PA
Very happy with the repair. Hoping it lasts and I won't have a leak again.
Gail - Coatesville, PA
Great Service. Nice people
LuAnn - Coatesville, PA
We love Nat. We does a great job. He is on time and meticulous.
They are more interested in fixing the problem then just trying to sell you something
Andrew - Coatesville, PA
David - Coatesville, PA
DIBIASE does it right! After making the appointment it was confirmed, I received a reminder, on the day of the appointment I received an email with a picture of the gentleman who would be doing my tune up. Nate could not have been more friendly, polite, or professional.
Sue - Coatesville, PA
Excellent service. Nathan is very diligent and an asset to your company
Great service – pleasant efficient employee you have in Nate
Richard - Coatesville, PA
Great service – pleasant and Knowledgable employee Nate
Ted - Coatesville, PA
Follow up call to check on water heater installed 3 months ago. Replaced fitting with history of failure at no charge.
Good price, knowledgable and helpful staff
Lisa - Coatesville, PA
I was able to schedule the job quickly and communication with Joe was great. He responded too my questions in a timely manner and answered all questions throughly. Technicians arrived on time, were knowledgable and communicated as needed.
Performed Quality Assurance, went over system Peco account 41929-01804 system settings ok installation looks good
Performed ac check up, check electrical low and high ok flushed drain test pump check split ok outdoor unit 410 pressures capacitor and contactor ok informed customer about age of water heater would recommend repla
Performed ac check up check electrical low and high ok filter ok check split, flushed drain ok replace blower capacitor, check outdoor unit 410 pressures capacitor and contactor ok installed hard start kit app8 cycle unit ok
Performed Inspection of Burnham Oil Boiler. Removed Burner Assembly and replaced Oil Nozzle. Cleaned and reset Electrodes. Changed Oil Filter and Cleaned Assembly. Removed Flue Pipe to Clean Chimney Base and to Clean Heat Exchanger on Boiler. Reassembled and used Furnace Cement to seal around Chimney Base. Put Boiler in operation to test. Bled Oil Line of Air. Performed a Combustion Test, Draft Test, and Smoke Test on Boiler. Smoke Test was measured a Trace at 1. Combustion and Draft Tests all measured within standards. Monitored system to ensure it was Heating properly. Water pressure in System was low at about 5 PSI. Added water to system to increase pressure to around 10 PSI. System is operating to standards at this time.
Performed Quality Assurance On AC System. Taped Insulation around bottom of Return Flex. Reviewed with customer any questions/comments she had about the system and installation.
Performed 8 ac outdoor units and 7 air handlers tuneups, two systems are twin, check electrical low and high ok flushed drain test pump check split ok replace all filters, check outdoor unit pressures r22 ok capacitors and control cycle units ok for unit number #2 found condenser fan motor seized and open run capacitor quoted for repairs customer ok installed new fan motor and new run capacitor test and cycle unit ok all splits units currently are in working condition, We will return some time next week to perform all rooftop systems check ups, Replace condenser fan motor for unit number #2
Reclaimed and removed old equipment. Installed whip and disconnect, new leveled pad, new line set and 24v wire. Installed new 2 stage gas furnace and evaporator coil. Reconnected to existing supply and return ducting. Taped all seams. Installed txv and brazed joints. Pressure tested and evacuated down to 287 microns. Installed new ez trap and condensate pump. Ran vinyl into septic line. Installed new receptacle and switch. Installed length of gas pipe and leak tested. Reconnected venting. Wired low volt safety's to aux terminal on Amana board. Delta t 22. Temp rise 46. Tested combustion and adjusted gas pressures. Everything operating to specification at time of service.
Performed ac check up, check electrical low and high ok clear trap and flushed as much as possible, replace filter, 16x25x1 check split supply 51 return 72 check outdoor unit r22 pressures contactor ok found 70/7.5 reading 65/7.5 also found disconnect not operating correctly canâ€™t pull it out to shut power off to unit, there are couple recommendations, cycle unit ok
Performed Precision AC Tune Up on the Main Air Handler and the Meeting Room Air Handler which are supplied by the Chiller System. Replaced the 8 - 20x25x2 Air Filters for the Main Air Handler and the 2 - 16x25x2 Air Filters for the Meeting Room Air Handler. Checked Condition of Blower Belts and adjusted the Tension on the Main Air Handler Blower Belt. Put Systems in operation and checked Cold Water Supply and Return Temperatures on both Systems. Checked Pneumatic Control Panel and Gauge Pressures. Inspected the Air Compressor. The Air Compressor may need to be filled with Lubrication Oil and the Air Filter needs to be cleaned/replaced. Will review manufacturer specifications and follow up if needed. System is operating to standards at this time.
Installed new heat pump and outdoor unit inside we installed a new heat pump with with a new ez trap and condensate pump. We ran a new lineset and thermostat wire to the outdoor unit. Vinyl was ran to the discharge line out side we installed a heat pump on furnace feet and a new whip and disconnect as well. Form for installation must be completed by service tech finished up installation settings, start up, let unit run in ac mode for 30 mins super heat and sub cooling ok 10 super heat and 9 sub cooling supply temp 49 return air 70 check and test 10 kw electric heat, went over all settings ok both heat pump and electric heat ok, final charge for heat pump was factory charge test pump ok
Performed ac check up, check electrical low and high ok replace filter, flushed drain ok check split, outdoor unit r22 pressures ok capacitor and contactor ok found blower wheel dirty, and condensation trap was partially blocked, cleared drain line quoted for repairs new ez trap and clean blower wheel
Performed ac check up, check electrical low and high ok replace filter, check split ok supply 53 return 75, could not flush drain there no excess to flush drain recommend ez trap installation, check outdoor unit r22 pressures contactor ok found capacitor reading 52 rated at 55 quoted for repairs, also informed customer about age of water heater would recommend replacing water heater and some water protection
Performed propane boiler check up, condensing boiler, wall hung, clean trap and flushed with water test pump, clean flame sensor/igniter check Inputs and outputs ok warm weather shutdown, test boiler only one zone is active combustion test ok water pressure and temp ok cycle boiler ok summer shutdown is set to 69
Performed cooling maintenance, replaced standard air filter. Inspected cooling coil. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Performed cooling maintenance, replaced rp213 media filter. Checked voltage, amperage and electrical connections, measured capacitor values ok. Inspected cooling coil, cleaned condensate drain and pump. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed certified heat tune up on Goodman gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out all condensate tubing and pressure switch lines. Cleaned flame sensor and inspectected burners. Tested furnace with a combustion analyzer. Gas furnace is working fine at time of service.
Found indoor and outdoor heat pump both running, but compressor sounding horable. Checked r22 pressures they were 137/98 , compressor is just plane shot system is a 1989. Recommend replacement. Homeowner and his wife are both school teachers and very busy would like if possible to just be emailed a quote for replacement.
Performed Precision AC Tune Up on Amana Heat Pump System. Replaced 16x20x1 Air Filter. Cleaned EZ Trap and cleared Drain Line from Union Fitting. Inspected Electrical Components and Electrical Connections on Indoor and Outdoor Units. Found an exposed section of thermostat wire on the Black Wire at the Air Handler. Stripped exposed wire and reconnected. Measured Refrigerant Charge on system. System is operating to standards at this time.
Installed Aprilaire 2410 he filter rack. Showed homeowner how to remove filter and re install. Tapped and secured all seems.
Attempted to start ac system for library. Chilled water pumps started up but chillier would not come on. Found chiller off on fault 3. Need to locate manual on control system.Went back with manual and attempted to reset control system on unit, Controls are not responding in accordance with manual, none of the LEDs are lighting up on left side of Comfortlink module. Board may require replacement and programming may be required. Need to get in contact with Carrier services to repair issue.Referred Penny to call Carrier Commercial Services. Tech from Carrier was on site 5.23.2019 and was able to rest control using programming tool. He will check system to get running again.
Performed ac check up, check electrical low and high ok flushed drain test pump ok filter ok, check split ok supply 47 return 68, check outdoor unit 410 pressures capacitor and contactor ok cycle ac unit ok
Performed precision ac tune up on York ac. 16x20x1 air filter is clean. Checked all electrical conections and components. Blew out condensate drain. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
As I entered the mechanical room could smell a strong smell of gas . Sprayed down gas lines and found a leak at the drip leg cap on water heater installed through Home Depot in 2017. Removed cap and re sealed with pipe dope and re checked for gas leaks no leaks now are present. Also found no saftey on condensate drain above second floor recommended an ez trap. She may conside installing at a latter date. Also performed precision ac tune up on carrier ac. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor unit. Ac system working fine at time of service.
We installed an air handler in the attic and a new outdoor air conditioner. The outdoor was installed on a new pad with a new whip as well as disconnect and new seal tite over power wire. Line hide was ran to cover the new linesets outside coming down the side of the house we installed a new line set and thermostat wire to the outdoor unit. We installed the air handler on 2 sets of heat pump feet for our air handler to sit on, to ensure proper pitch. We installed a wet switch in the pan as well as a new pan, and an ez trap as well for extra protection we installed a new honey well uv light in the coil for bacteria growth protection, we ran a new junction box and power wire with an outlet for the uv light to plug into. The unit was Triple evacuated and vacuumed. Reached 388 microns, held for 15 minutes. We charged the system with a pound of refrigerant and the pressures checked out ok. Filter size 14x20x1
Performed cooling maintenance, replaced standard air filter, cleaned condensate drain, inspected cooling coil. Checked voltage, amperage and electrical connections. Measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.