DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Coatesville, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Coatesville, PA.
for Coatesville, PA
Our Reviews by City
Great service – pleasant efficient employee you have in Nate
Richard - Coatesville, PA
Great service – pleasant and Knowledgable employee Nate
Ted - Coatesville, PA
Follow up call to check on water heater installed 3 months ago. Replaced fitting with history of failure at no charge.
Good price, knowledgable and helpful staff
Lisa - Coatesville, PA
I was able to schedule the job quickly and communication with Joe was great. He responded too my questions in a timely manner and answered all questions throughly. Technicians arrived on time, were knowledgable and communicated as needed.
Stephen - Coatesville, PA
I made the right decision to contract with DiBiase
Excellent service because of well-trained employee
Richard - Coatesville, PA
Concise evaluation of heating system
Kerry - Coatesville, PA
Like always - complete pros - did great work
Amy - Coatesville, PA
Marcus - Coatesville, PA
Bryan came out before my scheduled time which was great. He found the issue right away. Explained everything to me and gave me a quote before performing repairs. While fixing one issue he brought my attention to another issue....not looking for more business just making me a more aware customer. I thought that was great. Again gave me a quote with "No Pressure" to have the work done right then. I will strongly consider them again for future issue. Thanks Bryan!!
Warren - Coatesville, PA
Friendly tech and very knowledgeable
Ken - Coatesville, PA
Bryan was typical of the service I expect from Joe DiBiase. The reduced fee for an annual inspection is a good value. He was thorough in the inspection of my heat pump system and took the time to explain and answer questions. He made appropriate recommendations of additional products and services that they offer.
Always Great Service!
Tameka - Coatesville, PA
As a Realtor, I have referred and used DiBiase several times over the years. Can't say enough great things about Joe, his technicians and staff - they're all fantastic! Today Bryan performed an HVAC Certification for one of my sold listings, and he was phenomenal. If you're seeking a highly professional HVAC company, that charges a fair price and who is reliable and works with integrity, then your choice is DiBiase. Thanks Bryan for all your help today! Joe is lucky to have you as a member of the team!
Quick Response and great service
Judy - Coatesville, PA
I think it was a total of 1 hour from the time I called to the time everything was fixed. Truly appreciate it on such a hot day! Bryan was fantastic and did a great job!
Linda - Coatesville, PA
Arrived on time, very pleasant, efficient , and professional.
Amy - Coatesville, PA
Excellent Service. Friendly and knowledgeable technician.
Great and reliable
Joe - Coatesville, PA
An awesome company! I've used them for years!
Joan - Coatesville, PA
Nate was awesome
Darlene - Coatesville, PA
Nate answer all my questions and did a great cleaning on my heater and one has done before I am hoping this take care of all the problems
Great Service. Bryan is excellent!
Lisa - Coatesville, PA
Bryan is always friendly and professional. Top notch!
New HVAC Replacement
Justin - Coatesville, PA
No one ever wants to replace their HVAC when it breaks but these guys did a great job in replacing my furnace and AC unit in less than 2 days. When the old one stopped working they had a sales person out within 20 minutes to go over options. I solicited two other quotes and got comparable numbers before deciding to stick with these guys. They kept the space clean, didn't need me for much and work was completed to my satisfaction.
Upon arrival found bad blower motor. Needs replaced . 1/3 hp 1075 230v. Small system and will need blower bracket as well.Due to age and condition recommend replacing system. R-22 old and not maintained
Upon arrival found unit low on charge. Added refrigerant and dye to bring to standards.
Performed precision ac tune up. System is running to manufacture specifications. Filter 213 replaced
Performed precision ac tune up . System is old and running to best that it can. Pressures a little high. Replaced air filter 16/25/4.Also purged and flushed hot water heater. Tested operation
Performed precision ac tune up. System is running to manufacture specifications.
Drained water heater to below top water line. Removed webstone push to fi fittings and installed new Shark adapters for water heater. Reconnected piping. Filled and tested water heater.No charge - recall.
Performed precision ac tune up. Changed filters for both air handler systems, one in the attic and one in the basement. Found attic air handler motor belt to be worn. We recommend replacing. Estimate will be included. Checked temperature splits and pressure readings for pneumatic system. System is running at manufacture specifications. During tune up, we inspected the belts for the blower motor in the attic air handler and we recommend that they need to be replaced. They are worn from everyday extensive use. Replacing these belts will ensure they will last through the summer season and maintain airflow through main building. There are two belts on the motor, their size is B78.Replaced belts and tested ( b78)
Performed quality assurance inspection and ac tune up. System charge was Dailed in and tested. Unit is running to manufacture specifications
Unit not cooling and strange odor in home. Found condensate pump level switch tripped and no power to pump. Found GFI tripped and outlet corroded. Moved plug to other outlet where GFI is located. Tested system operation and replaced system air filter.Recommend annual system maintenance with service plan.
Upon arrival found unit outdoor unit locked out flashing 3 code . Intermittent y connection. Removed peco box from the y connection. Tested operation and charge. Also gathered amp reading on compressor at 6. Checked all wiring connections. System charge low 129 sh 4 high 334 sc 7.7. System is running to manufacture specifications at this time.
AC install. Installed indoor coil and outdoor unit . Reattached drain line to coil . We reattached duct work to coil . We flushed and pressure tested the line set . We evacuated and charged the system to factory standards. We reconnected the high and low volt wires to outdoor unit . We tested the overall system and the system is running to factory standards.
Removed old water heater and installed new 50 gal water heater. Added new ball valve and T fitting for expansion tank. Adjusted vent pipe accordingly to fit new water heater as it is bigger than last model. Filled, tested pressured operations. System will take about 2-3 hours to heat up water.Customer declined option for waterpan and water alarm.
Performed precision heat tune up. System is running to manufacture specifications. Changed filter 161/25/1
AC Tune Up . Checked filter/Clean . Cleaned condensate Pump and trap. Checked Capacitors on indoor and outdoor units . Tested electrical wiring and connections. Tested amp draws and voltages . Tested airflow, temperature splits and refrigerant charge. Checked contactor on outdoor unit/ok . Tested overall system and system is running to factory standards.
Removed all discs and found two runs that only part of the ducting was cut in which opened completely by cutting the proper hole . all runs are at full air flow at this time.
Replaced furnace and air conditioner for home, reinstalled humidifier . Install new line set, new T6 thermostat, new 2" venting system for furnace to outside . Capped off chimney connection. Tested system and system is running to factory standards.
Upon arrival found male connection cold water side corroded . Also the relief valve is dripping . Checked water pressure at 60psi and the expansion tank is good. Due to age and condition recommend replacing. Hot water heater is 12 yrs old.Also would like a quote to replace the ac system . Outdoor compressor went last year. System is 12 years old.
Upon arrival found outdoor unit in lockout. Found loose connection on thermostat wire. Reconnected and tested operation. Checked charge. All ok
Performed precision heat tune up. Recommend replacing both units due to age and conditon.Main floor unit has a new Goodman coil just installed . Still r-22 . Not picking up great splits . Model and serial on indoor coil ripped off. Home shield put it in. Still same outdoor unit which is old and name plate worn off. Terrible condition. . Replaced filter 16/25/1.Bedroom unit temperature splits are only 7 degrees . Low on charge. Unit is old and worn. R-22 . Filter ok 16/25/1. Unit not cooling .
Performed precision ac tune up. System is running to manufacture specifications. Filter did not need changed at this time . Please renew maintenance contract. This is our last visit unless you Renew the maintenance contract. Call the office to renew
Performed precision heat tune up. System is running to manufacture specifications. Filter was changed 16/25/1.
Found shark bite fitting faulty on inlet connection at hot water heater. Replaced with new and the same thing occurred. Removed both fittings and soldered the copper side and connected the other side(hot) with cpvc connection with glue. Cleaned water up. Shark bites have been totally removed from the system. Installed new water alarm as well.
Installed new Amana heat pump and Amana air handler. Installed new 15 kw emergency heat kit for indoor air handler. New TXV was installed along with some new duct work for the air handlers supply. Outdoor unit was leveled on a pad and is sitting up on snow feet, a new disconnect was installed. System was evacuated down to 300 microns and we tested the system in Heat and cool and it is running to factory standards.Heat temps- 117 degrees on supply, 58 degree temp on return.
Performed Gas Furnace Inspection on Comfortmaker Furnace. Replaced 16x25x1 Air Filter. Cleaned Drain Line for the Furnace and Air Conditioner. Excercised Pressure Switches and Cleaned Flame Sensor. Inspected Heat Exchanger and Burner Assembly. Measured Manifold Gas Pressure while performing Combustion Analysis Test on Furnace. All Combustion numbers and Gas Pressure were to standard.Drain Pipe for the Relief Valve on the Water Heater was not to Standard, and was more than 6â€ from the bottom of the Drain Pipe to the Floor, as per Home Inspection. Repiped using 3/4â€ PVC and Fittings. Relief Valve Pipe now extends to the bottom of the Water Heater, which has a 3â€ clearance to the Floor.
Performed precision ac tune up. Could not clean condensate pump due to the fact it is hard piped in. System i running to operational standards at this time.Filter did not need to be changed