When it comes to your Downingtown, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Downingtown, PA to see how we live up to these values every day, in every way.
for Downingtown, PA
Our Reviews by City
Great service and excellent tech.
Lois - Downingtown, PA
Kurt did an excellent job on changing the position of the exhaust vent. Very happy with the solution to the problem.
follow up service on new equipment
Patrick - Downingtown, PA
Maribeth - Downingtown, PA
I felt that Brian new what he was talking about and was honest about the condition of our units.
Professional & On-time
Lee - Downingtown, PA
The Technician, Kurt, was on-time, professional and I really appreciated the fact that he turned off the lights after he was done in both areas he was checking. It's a small thing, but it just goes to show you that the staff are detail-oriented when it comes to service. Job well done!
Brian - Downingtown, PA
Great service as usual.
Charles - Downingtown, PA
Arrived ahead of time, answered all my questions and completed their tasks with a professional attitude. Great team.
New Mini Split
Charles - Downingtown, PA
Mike and Andy did a great job installing my Mini Split system in our sunroom. The guys were friendly, hard working and able and willing to answer all questions. They started working at 8:00 AM and didn't stop until the job was done. Kudos to two talented young men.
Heater service - very thorough
John - Downingtown, PA
Great service and communication. Quick but thorough.
Robert - Downingtown, PA
Very friendly, and efficient. Would highly recommend.
Barbara - Downingtown, PA
Polite knowledgeable techs
Kim - Downingtown, PA
Always professional and courteous
Paul and Dave are excellent service techs. They are competent and personal.
Lois - Downingtown, PA
Rich - Downingtown, PA
Great service and great people. We are always highly satisfied with the work performed by DiBiase team!
Mary - Downingtown, PA
Leslie - Downingtown, PA
Great service and arrived right on time. Explained all repairs to me and showed me pictures of the items to be repaired.
Great service and price
Andy - Downingtown, PA
Very professional team who quickly got job done
Their service as usual is fantastic.
Steven - Downingtown, PA
Andy - Downingtown, PA
Very satisfied with the service on our heat pump.
William - Downingtown, PA
Jim - Downingtown, PA
Good- thanks to Chris for the quick service
Bob - Downingtown, PA
My wife and I were devastated that our AC went on one of the hottest weeks of the summer. On Tuesday we were informed our system was done. Although we could have requested just the AC it was pointed out that the heating system was the same age. Had I not dealt with Joe for these many years I probably would have assume he was just up selling me. Rather I knew he has never done that before. Back to installation, which was accomplished on Friday. Later follow to be sure everything was set up correctly, assured us that things (AC) was running correctly. In all happy to continue to deal with Joe.
Good professional prompt service
Nikhil - Downingtown, PA
Great Service at a moments notice
Austin - Downingtown, PA
Had my AC fail in a heat wave and Chris was slotted in to take a look at my system ahead of schedule. He came out and diagnosed my problem and was able to replace the parts and service the heat pump quickly and easily.
Rati - Downingtown, PA
Tony - Downingtown, PA
Performed heating maintenance, checked media filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate trap. Checked voltage, amperage and electrical connection. Started gas furnace, measured fuel pressures, tested limit and safety switches. Performed combustion test and checked temperature rise.
No heat, upon arrival found heater off, set thermostat to call for heat, found gas valve not opening, getting 24 volts but not opening, quoted for new gas valve adjust gas pressure, performing a efficiency and combustion analysis customer ok with repairs, installed new slow opening valve and adjust gas manifold pressure set to 3.5 inches water column cycle heater and performed combustion test co levels, ok
Install powered humidifier in place of Honeywell steam humidifier change drain on wall no bow anymore
Cut of existing exahaust pipe at outside termination. Re- piped exahaust termination with3â€ 45and 3â€ 90. Angled termination away from condenser unit , and away from chimney. Also made sure foam stayed intact at inside wall.
Performed precision heat tune up on Williamson gas boiler. Vacuumed out burners and checked inside boiler and at chimney base for debris. Found expansion needed drained Down. Recommend we drain it, homeowner will drain himself. Cycled boiler in heat mode, and performed combustion test. Gas boiler is working fine at time of service, but recommended he drain the tank before heating season gets going.
Replace second floor inducer, removed failing inducer assembly. Cleaned mating surface. Install new inducer. Wired new inducer. Set gas furnace and checked operation. Checked inducer amp draw, found running normal.
Replacement of 75 gallon propane hot water heater.( homeowner does not want re Circe pump and keep expansion tank original. Put new water heater in pan on bricks with water alarm. Checked pressure at 60 psi customer to pay for humidifier replacement today.to install 12 pm on 10/22/19
Performed 6 month inspection on American standard gas furnace. Aprilaire 413 air filter ok. Tested gas pressure and performed combustion test. Checked operation of drains. Tested humidifier. Gas furnace is working fine at time of inspection.
Performed heating maintenance, checked air filter ok. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, checked fuel pressures ok. Tested limit and safety switches. Performed combustion test. Checked operation and temperature rise.
Found electrodes very worn. Replaced electrodes. Also performed precision heat tune up on oil boiler. Replaced rf1 oil filter. Replaced 1.00 80b nozzle. Vacuumed and brushed inside boiler and chimney liner at base. Oil boiler is getting older but still working at this point.
Preformed a precision heat tune up on the heat pump, changed filters blew out drains tested back up heat and heat-pump both met manufacture standards. Capacitor for outdoor getting low. Customer renewed service plan.
Preformed precision heat tune up checked charges and backup heat outdoor went into defrost mode blew out the drains and changed the air filter. Everything checked out ok, unit is running to factory standards.
Performed precision heat tune up on thermopride oil furnace with trane heatpump. Replaced 20x20x1 air filter. Replaced.75x70a nozzle. Replaced garbar oil filter. Performed combustion test on oil furnace. Checked operation of heat pump reversing valve. Also serviced humidifier with #35 humidifier pad. System is working fine at time of service.
Performed Quality Assurance on American Standard Heat Pump system. Tested operation of Humidifier and set to 35%. Completed Checklist form in system. Rewired Pump/EZ Trap safeties so they would break R at the Control Board. Reviewed installation with homeowner.
Performed precision heat tune up on luxaire gas furnace. Replaced 16x25x1 air filter. Checked and adjusted gas pressures. Blew out condensate drain. Found no surge protection on ecm blower motor, recommended to install. Performed combustion test. Gas furnace is working fine at time of service.
Customer seen water coming from relief valve, upon arrival no water was leaking check water pressure and was reading over 30 psi lowered pressure and inspect gage, gage climbing up found water feeder is letting water into system, informed customer situation and bypassed feeder by shutting off valve and manually add water to system, recommended installing new relief valve and also drain expansion tank customer ok with repair made necessary repairs and cycle boiler system bleed air from system And check floor water flow and heat rejection ok
Found flame sensor pitted and ecm motor not protected. Replaced flame sensor and added surge protector to blower moter. Performed precision heat tune up on trane gas furnace. Replaced Aprilaire 501 ( homeowner provided) checked all electrical components and connections. Performed combustion test and checked gas pressures. Blew out condensate drain. Also found Honeywell steam humidifier not functioning correctly. If system is drained it will not refill not worth fixing due to possible control issue. Recommend replacing with ether another stem humidifier made by Aprilaire, or a powered humidifier. Gave homeowner both options. Homeowner to have propane water heater replaced.
Performed leak search on heat pump unit found evaporator coil leaking dye sign on indoor coil quoted for repair due to age and price to repair would recommend having price to replace heat pump system
Performed precision heat tune up on trane oil furnace. Washable air filter is clean. Replaced .75 80a nozzle. Replaced rf1 oil filter. Pump screen is ok. Vacuumed soot from smoke pipe and heat exchanger. Performed smoke and combustion test. Oil furnace is working fine at time of service.
Performed geothermal heat check up check electrical low and high ok replace filter customer provided, check electric heat back up ok check compressor cap and electrical ok check split water in and out temps ok cycle unit ok
Performed heating maintenance, replaced standard air filter. Blew out condensate trap. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, checked fuel pressures, found manifold pressures low. Adjusted manifold pressures to 3.5â€ checked operation. Performed combustion test, found now that fuel pressure was increased to 3.5â€ furnace co increased to 135 ppm. Adjusted manifold pressures back to 2.5â€ checked co reading now normal at 45 ppm. Checked furnace operation and temperature rise. Heat exchanger is becoming restricted and is beginning to show signs of failure.
Performed precision heat tune up on Gibson gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked gas pressure and performed combustion test. Cleaned flame sensor . Also serviced humidifier with #10 humidifier pad. Gas furnace is working fine at time of service.
Checked no complaint, found heat call at aqua stat and call to burners. Checked limit and safety switches, found spill switch had a good spade connector not plugged in to the switch. Found that it was connected between plastic insulation and spade. Reconnected spade connector. Started boiler and checked boiler pressure and temperature.
Performed precision heat tune up on trane gas furnace. Replace 20x20x1 air filter. Blew out condensate drain. Checked temperature rise. Cleaned flame sensor, and checked gas pressure. Trane gas furnace is working fine at time of service.
Performed heating maintenance, checked media filter ok. Checked voltage, amperage and electrical connections. Cleaned burners and flame sensor, inspected heat exchanger. Started gas furnace, measured fuel pressures, performed combustion test. Checked operation and temperature rise.