When it comes to your Downingtown, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Downingtown, PA to see how we live up to these values every day, in every way.
for Downingtown, PA
Our Reviews by City
Their service as usual is fantastic.
Steven - Downingtown, PA
Andy - Downingtown, PA
Very satisfied with the service on our heat pump.
William - Downingtown, PA
Jim - Downingtown, PA
Good- thanks to Chris for the quick service
Bob - Downingtown, PA
My wife and I were devastated that our AC went on one of the hottest weeks of the summer. On Tuesday we were informed our system was done. Although we could have requested just the AC it was pointed out that the heating system was the same age. Had I not dealt with Joe for these many years I probably would have assume he was just up selling me. Rather I knew he has never done that before. Back to installation, which was accomplished on Friday. Later follow to be sure everything was set up correctly, assured us that things (AC) was running correctly. In all happy to continue to deal with Joe.
Good professional prompt service
Nikhil - Downingtown, PA
Great Service at a moments notice
Austin - Downingtown, PA
Had my AC fail in a heat wave and Chris was slotted in to take a look at my system ahead of schedule. He came out and diagnosed my problem and was able to replace the parts and service the heat pump quickly and easily.
Rati - Downingtown, PA
Tony - Downingtown, PA
Courteous, friendly and profession
Bob and Deb - Downingtown, PA
Company wants your business and does the job to prove it.
Walt - Downingtown, PA
Louis was courteous and pleasant
On time, courteous, helpful when problems occurred.
Bob - Downingtown, PA
Good to have long term relationship with reputable company. Looking forward to the new Heating/AC system. Unfortunately it can’t happen fast enough during this heat wave. Can’t imagine being at the bottom if we were not already a revgular customer.
Mario - Downingtown, PA
Barbara - Downingtown, PA
Kurt, our tech was timely, courteous and knowledgeable
Greg - Downingtown, PA
Great work at great price
Joe - Downingtown, PA
Technician, Kurt, was very polite and professional. Arrived on time and cleaned the AC system and did a repair on unit. Work was done well and at a fair price!
Mark - Downingtown, PA
Kim - Downingtown, PA
Richard - Downingtown, PA
Great service but $180 for a 35 minute service call with no parts seems excessive. Problem was due to a clogged vent pipe leading from the drip tray below the condenser.
Great customer service
Jeanne - Downingtown, PA
Very responsive to me when I needed my air conditioning fixed. Willing to work with my budget and very clear with regards to estimate, work that needed to be done and making sure the install was done at a convenient day for me. Everyone I spoke to her work with was very professional and accommodating and I would definitely recommend this company to others.
Michael - Downingtown, PA
Service AC system
Ryan - Downingtown, PA
Leak in 5 year old Ducane system
Ryan - Downingtown, PA
Good tech, high prices
Robert - Downingtown, PA
Mimouna - Downingtown, PA
Very informative, polite and professional!
Performed ac inspection tune up, on heat pumpkin check electrical low and high ok replace filters, found water inside secondary pan, inspect drain line ok, there was some restriction inside primary pan, cleared restriction, and inspect pan, found a hole on primary pan, seems like water is being leaking for while, water is slowly draining from primary pan all the corrosion and settlement from metal pan, outdoor unit r22 pressures ok capacitor and contactor ok, also insulated about 12 inches of suction pipe, aversion condition of unit poor, unit needs to re replace before water damage happens took pictures of condition
No power to unit place is vacant need to check with Dave if he wants this unit serviced
Performed two ac check ups, replace both filters, check electrical low and high ok flushed drain ok traps and pump ok, check split ok outdoor units 410 pressures capacitor and contactor ok one unit is single ac and other is heat pump with electric back up, cycle both units ok
Performed ac check up on roof top packaged unit replace both filters, clean trap and flushed trap ok check electrical low and high ok capacitor and contactor ok r22 pressures ok cycle unit ok
Could. Not get unit to run power is off to unit and it is vacant property, they usually turned power off to vacant places
Performed ac check on rooftop package heat pump, check electrical low and high ok replace both filters, clears drain line, noticed evap coil dirty clean as much as possible with a brush, check capacitor and contactor ok all within limits refrigerant pressures r22 cycle unit ok
Performed ac check up in roof top package heat pump check electrical low and high ok flushed and cleared drain line ok try to clean evaporator coil with brush, replace both filters, check refrigerant pressures r22 ok capacitor and contactor ok cycle unit ok Amp draw and voltage ok
Upon arrival found both thermostats not adjusting to temp, reset stats and replace batteries, recommended replacing thermostats due to customer having same issues since last week and las night, installed two new thermostats cycle and test units ok office to bill for payment
Checked no cooling complaint, set thermostat to cooling, compressor went off on overload and fan ran at 1/2 speed, found failed dual run capacitor. Replaced dual run capacitor. Started air conditioner, checked refrigerant charge. Signed out for maintenance plan need to schedule maintenance.
Performed two ac check ups, check electrical low and high flushed drain ok replace both filters, check split ok gentle flushed drain ok took pictures of drain condition, as right now drain line and an looks ok, replace 10 mfd condenser fan motor cap due to reading 4 check r22 pressures cycle both units ok
Performed ac check up, check electrical low and high ok replace filter, replace blower cap reading very low mfd, 7 rated at 10 flushed drain and test pump ok added tabs to pan, check outdoor unit r22 pressures ok capacitor and contactor ok 200/70 with 12 subccoling and 6 super heat supply temp 50 return air 66 Office to bill customer
No ac, water leaking, upon arrival found unit indoor and outdoor running, suction Line iced up, And half of coil frozen, check filter ok blower running ok, system is low in r22, explained situation with customer and gave him all his options, due to system running low in r22, and age, recommend replacing unit, also gave him options to add refrigerant which could leak tomorrow, next week, or next month, it is unknown to how long would it last,
Performed three rooftop packages heat pumps check ups check electrical low and high ok flushed trap check capacitor and contactor ok ok replace all filters, check refrigerant pressures all coils are clean cycle units ok
Perform calculations to determine the proper size ductwork to properly condition the space. We will install new duct supply runs in accordance with the calculations. We will measure the airflow to the space. 8/19/19 installed 2 8â€ supply runs to sunroom with one 10â€ motorized damper. Tested operation of of damper and air flow is very good. Left grills for homeowner to later install.
Performed AC Tune Up on Ruud System. Replaced the 20x20x1 Air Filter. Cleaned CondensatIon Drain Pipe from the Access Fitting. Inspected Electrical Components on the Indoor and Outdoor Units. Components are testing within their ratings. The Contactor for the Outdoor Unit is worn and pitted. This was noted and recommended on prior AC Tune Ups. Measured Refrigerant Charge on system.While System is operating, it would be recommended to begin planning/saving for replacement. The system is about 14-15 Years old and uses the old R-22 Refrigerant that is being phased out. If a Refrigerant issues occurs with the system, then it will be recommended to replace the system.Thank you for renewing your Service Membership today for your Oil Furnace/AC System!
Performed two roof top package units, upon arrival found units were off and left unit would not come on, found breaker tripped reset breaker and unit started ok replace filters, flushed drain ok check capacitors and contactors ok, added refrigerant to right aid unit running low sub cooling and high super heat, after adding refrigerant both units are working up to standard supply and return split ok all filter are located on rooftop unit, office to bill for payment
Checked condensate collecting on plenum band trunk. Found plenum and trunk wet with condensation, measured RH in the basement, got 67% measured dew point, got 57.checked deltaT, 71.2 return and 52.3 supply. Recommend installing dehumidifier to better control humidity Need a quote to wrap plenum and 45â€™ of trunk.
Installed customer supplied thermostat ecobee 4 with room sensor, set up thermostat to 2 heat pump with 1 stage back up, check and test all modes electric heat back up ok 20 kw ok ac and heat mode ok noticed and informed customer about outdoor disconnect not mounted in the wall hanging by the unit recommended attaching disconnect to wall
Installed a new air handler on top of a new box raised up on bricks and vibration pads. Installed a new heat pump on pump up legs with a new pad and disconnect box with a new whip to the heat pump. Flushed existing copper lines. Brazed and pressure tested up to 320 psi. Let vacuum down to 300 microns. Added 12 oz of refrigerant. Ran new condensate drain with an ez trap to termination in discharge pipe. Replaced new 20â€x20â€x1â€ filter. Installed a Aprilaire humidifier ran copper line to hot water piping for humidifier. Ran a new wire up to nest thermostat . Installed a 8â€ return up to the second floor and a new 6â€ supply to basement bedroom! Caulked and sealed all penetration in and out of house ! Unit is running at manufactures specifications.
Performed cooling maintenance, checked air filters ok. Inspected cooling coil. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Checked no cooling complaint, found thermostat blank, found low voltage fuse blown, checked for shorts, found no shorts or grounds, replaced fuse and after a minute it blew the fuse again, checked for shorts again, could only get a short with thermostat installed on subassembly. Removed thermostat, jumped out heat pump, energized o, y1, y2 all runs need to replace thermostat Andrew will look at thermostats and decide which one he wants.
Replace blower motor, removed failed blower motor and mount. Install new motor and mount. Wired motor. Install motor assembly. Started and checked operation. Set thermostat to cooling, checked refrigerant charge and temperature drop across coil.
Airflow was set to 5 ton ac, lowered to 400 cfm per ton total of 1400 cfm corresponding to 3 1/2 check all vents for proper flow ok, system ok this time, also replace ez trap due to leak at one of the joints, took picture of the inside coil
Installed a new heater , coil and air conditioner. Installed a new aprilaire humidifier. A t6 thermostat . Ran a new condensate drain with an ez trap new condensate pump ! Reconnected to existing duct work. Ac is on a new pad with a new disconnect and whip to the unit . Caulked and sealed all penetrations. Flushed existing copper lines and reconnected and brazed . Nitro up to 310 psi and let sit for 10 minutes! Let vacuum down to 300 micron added 10 oz of refrigerant to get a subcooling of 10.4 ! Had a 20 degree split between supply and return ! 50 degree temp rise when in heating ! Put in a new 16â€x25â€x1â€ filter
Found older heat pump package unit r22 pressures were 180/70. Talked to homeowner and he said his wife would say that the humidity feels higher than it should be but thermostat is maintains 70 degrees. They also had some sort of a burning smell so checked over blower motor and wiring, did not see any signs of burned wires or any odd smells. System is about 15 years old so I do recommend replacing of system do to age of unit. Called and set up appointment with office.