When it comes to your Downingtown, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Downingtown, PA to see how we live up to these values every day, in every way.
for Downingtown, PA
Our Reviews by City
Prompt and courteous
Ryan - Downingtown, PA
Alphonso - Downingtown, PA
Great, fast service
Alexander - Downingtown, PA
Brian was very helpful in fixing our heating unit. Luckily we already owned the part needing to be replaced and he was able to do so.
Good service. Reputable company
Umar - Downingtown, PA
Great experience. The DiBiase team was professional and efficient. Hopefully the AC tuneup will make it run smoothly for a while. Thanks!
Excellent and Personable
Crystal - Downingtown, PA
Paul was a pleasure to work with. He was punctual, informative, and efficient. He certainly went above and beyond to educate me and review all aspects of our heating unit. If I’m able to request Paul in the future, I certainly will. Thanks Paul.
Jim - Downingtown, PA
I think they are honest and reasonable
Sarah - Downingtown, PA
He was great as always. Thank you
Cindie - Downingtown, PA
Thank you so much for going the extra mile to make sure my family had heat again.
Great service and knowledgeable technicians.
Lois - Downingtown, PA
Brian and Zach fixed the leaking pipe. Excellent service and response time.
Robert - Downingtown, PA
Install of New Heat Pump
Ryan - Downingtown, PA
Robert - Downingtown, PA
They explained what they found an how they fixed it.
Sara - Downingtown, PA
Barbara - Downingtown, PA
Dibiase personnel are professional, efficient, and knowledgeable.
Just the best
Don - Downingtown, PA
Professional and thorough. Great job!
Ehren - Downingtown, PA
Great. On time, clean and professional work. Thank you
Annual HVAC service
Cyndy Mercedes - Downingtown, PA
Great service and siggestions
Patrick - Downingtown, PA
Service is key and they are the best in the area!
Nikhil - Downingtown, PA
William - Downingtown, PA
Having a SUPERTEAM to install our new system is beyond any service group we have ever had. From the minute they arrived, I knew we were in great hands & they exceeded all our expectations. I recommend this stellar team to all your customers. Mike, Zach & Andy are true professionals.
Tim - Downingtown, PA
The technician was prompt, professional and very courteous
Linda - Downingtown, PA
Tim - Downingtown, PA
Pam - Downingtown, PA
Technician was on time and through
Excellent, five stars
Steve - Downingtown, PA
Drained and removed old water heater. Replaced shutoff valve. Installed new expansion tank and copper piping. Installed new Bradford white 50 gallon electric water heater. Reconnected electric and tested elements. Tested water pressure and found to be high. Replaced old pressure reducing valve and set pressure at 50 psi. Installed water alarm in catch pan. Tested temperature. Water heater working fine at time of install.
Performed gas heat tune up, check electrical low and high ok replace filter, check gas manifold pressure ok combustion test cycle heater ok test condensation pump vinyl tubing should get replaced and Also noticed gas line is not bonded and has CSCCT BY code gas line should be bonded with in 3 feet entrance of the home emailed proposal for repairs customer will call Offcie for repairs,
Performed Quality Assurance on American Standards Gas Furnace/AC system. Reviewed installation with homeowner. Completed checklist form in the system.
Performed heat pump tune up. Checked all electrical connections and components. Found a loose low volt wire inside air handler. Checked electrical heat kit. Checked temperature rise. Replaced air filter. Inspected coil and lineset. Blew out condensate line. Checked refrigerant pressures and temperatures. Tested capacitor and contactor. Measure compressor amperage. Checked all electrical connections on outdoor unit. System is running well at time of service. Customer concerned with water heater performance. Checked water heater connections and components. Both elements are working. Adjusted thermostats. Checked amperage. Tested water hardness. Water is 13 grains hard. Water heater is 3 years old and could be losing efficiency due to scale build up. Took a sample from water heater drain and found scale build up. Recommend whole house water softener for hardness and other contaminants.
Performed peco heat pump check up, customer has propane furnace as back up, check electrical low and high ok filter ok, check split check outdoor unit pressures and electrical ok both coils are clean, noticed thermostat not set up correctly and also return 12 in flex disconnected to collar informed customer and emailed proposal to make repairs, also customer would like to add a second unit to other part of house please contact customer to schedule visit indoor coil is very hard to get to it, name plate is not visible
Performed propane gas heater check up check electrical low and high ok filter ok clean sensor and check gas manifold ok, check drain for furnace noticed drain hoses and vacuum hoses are starting to crack, also found burners with corrosion build up on cones. Would recommend replacing both items, and also blower wheel should be cleaned have to be removed and clean all fins with brushes and vacuum, emailed proposal
Performed precision heat tune up on burnham oil boiler. Replaced rf1 oil filter. Replaced.85x60a nozzle. Checked pump screen. Performed smoke and combustion test. Tennet talked about hot water issue, issue is not with boiler or mixing valve, issue is only with shower. She will contact landlord about issue. Boiler is working fine at time of service.
performed precision heat tuneup. Checked all electrical connections and components. Checked flue and ducts. Measured temperature rise. Performed combustion test. Measured gas pressure. Tested Capacitor and found to be weak. Replaced capacitor. Blew out hoses in furnace. Cycled heating system. Replaced air filter. System running well at time of service.
Performed oil boiler tune up/cleaning, check electrical low and high, replace oil filter, nozzle and pump strainer, clean and adjust electrodes ok, purge air from oil lines cycle burner ok, clean heat exchanger and flue pipe, cleared chimney base ok, performed smoke and combustion test ok, check draft ok, during testing found several issues that were brought to customer attention, water pressure is 5 psi water feeder to regulating pressure, also found expansion tank with little pressure in it, and pressures temperature gage out of control not reading accurately, some of the valve are very hard to turn and also have some rust around them, highly recommend having repairs done to prevent Any damage to system, replace expansion tank, new automatic fill valve, new pressure temperature gage and also replace air scoop with new air eliminator cycle boiler test limit ok purge all air from system and check both floors and both floors baseboard are getting hot check for water leaks on worked per
Removed the old heater ,coil and ac unit. Installed a new amana gas heater on feet and reconnected the gas piping and adapted. Reconnect return duct and reattached humidifier. Installed a new amana coil and adapted all duct work as needed. Taped and sealed all duct. Ran a new condensate drain with an ez trap and heater drain into existing discharge in to ground. Reattached flue piping and performed a combustion test. Installed a new amana ac unit on top of a plastic pad with bricks. A new disconnect box and whip go to the unit. Flushed coppers lines and brazed and leak checked with nitrogen and soapy bubbles. Let vacuum down to 120 microns . Cracked charge. Tested equipment in both heating and ac installed a new t10 thermostat and tested stat.
Found pitted 1 1/2 pole contactor. 1/7/20. Replaced 1 1/2 pole contactor and tested heat pump
Looked over installation of replacing customer supplied heater. Took photos of unit and provided estimate to replace. Homeowner is not going with us at this point, told him that if we had to return there will be a return visit fee of $65.00.
Performed precision heat tune up on American standard gas furnace. Homeowner just replaced Aprilaire 201 air filter. Checked all electrical conections and components. Cleaned flame sensor. Blew out condensate drain. Checked gas pressure and performed combustion test. Checked temperature rise. Gas furnace is working fine at time of service.
Performed quality assurance on amana gas furnace. Checked air filter, air filter ok. Gave instructions to replace 16x25x1 air filter every 3 months. Checked all electrical conections and components. Checked gas pressure and performed combustion test.
Performed peco heat tune up on trane heat pump. Found Aprilaire 201 air filter needs replaced ( homeowner to replace). Checked all electrical conections and components. Checked temperature rise on heat pump and only had 11 degree temperature rise. Checked refrigerant pressures and found r-22 system low on charge. Pressures were 155/28. Recommended replacement of heat pump system. Called and set up appointment with office for bill to come out.
Performed Six Month Heating Inspection on Amana Gas Furnace. Replaced 16x20x1 Air Filter. Inspected Electrical Components and Fan Speed Settings. Inspected Condensation Pump and Furnace drain lines which were clean. Measured Manifold Gas Pressure while performing Combustion Analysis on Furnace. Adjusted Gas Pressure slightly while testing combustion levels. System is operating to standards at this time.
Found furnace tagged out with a lockout tag on the furnace but power switch on. Went over gas furnace heat exchanger with an inspection camera. Found a lot of pitting in the heat exchanger. Recommend to her that she should definitely replace the furnace, and also recommended replacing the a/c due to it being a 2003 to get the warranty on entire system. Called and set up appointment with office for bill to come out.
Removed old heater and coil and replaced them with an American standard gas furnace. Installed a new American standard coil on top and adapted all duct work as needed . Taped and sealed all duct work. Installed a new Aprilaire high efficiency filter. Reconnected gas piping and adapted as needed. Checked for gas leaks. Reconnected humidifier condensate line and adapted to the new coil drain. Installed an ez trap on to the condensate pipe. Put in a new condensate pump and ran new vinyl tubing over to discharge pipe. Ran new copper lines to the new outside American standard Ac unit. Brazed and leak checked all joints with 300 psi of nitro and spray bubbles. Put new Ac on a plastic pad with stones underneath. New disconnect box and whip to unit. Ran new flue piping to outside near the Ac unit. Caulked and sealed all penetrations into the house. Ran a new electrical wiring down to a new 4x4 box with a switch and an outlet. Capped off old chimney . Tested system and everything is working as
Performed heat pump check up check electrical low and high ok replace filter and service humidifier test electric heat back up check split ok check outdoor unit pressures capacitor and contactor ok check defrost ok cycle heat pump ok
Performed two gas propane furnaces check ups, check electrical low and high clean flame sensor and check manifold pressures ok combustion test cycle furnaces check splits ok replace both filters, customer proved 413, service humidifier replace pad and test ok
Checked over original copper vent and fill piping. Would replace with black iron pipe. New tank alarm whistle combo. Condition of oil tank is ok at this point. Also vent and fill cap. Seal over exsisting piping at wall.
Performed Quality Assurance on Oil Furnace. Completed Checklist Form in system. Sealed Flex Duct Take Offs on main trunk. Increased airflow on blower. Took Temperature split readings. Supply 143, Return 75 after increasing fan speed. Reviewed installation with Homeowner.
Performed gas heat check up check electrical low and high ok clean sensor check filter and test humidifier ok, check and test pump ok, burners should get replaced due to flame backfiring sometimes, end cones are very corrupted and have lot of build up blocking preventing propane flow, when checking gas pressures furnace runs on low stage all the time zone board not bringing second stage of heat, check operation second stage come in when set temps is below 90 with 20 differential, customer has issues with same board during cooling season, due to overall required repairs would recommend replacing system with new zoning control
Installation of humidifier for first floor system, will reduce electro static, will maintain humidity levels in the winter time,
Drained down and removed old water heater. Installed a new Bradford White 50 Gallon Natural Gas Atmospheric water heater in an Auxiliary Drain Pan. Installed the Flood Stop Alarm with Shut-Off Valve. Tested water temperatures and water pressures upon completion. Clean and service humidifier and test operation.