DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the East Fallowfield Township, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in East Fallowfield Township, PA.
for East Fallowfield Township, PA
Our Reviews by City
Matt - East Fallowfield Township, PA
Gail - East Fallowfield Township, PA
Tech Paul, Arrived promptly, and was very knowledgeable. After a through inspection, trying to find the issue, he determined all my system needed was a good cleaning. I was so impressed with the amount of time he took that I signed a maintenance contract. Lastly, I should add I’m a new customer!
Follow up and Semi Annual Maintenance
Bill - East Fallowfield Township, PA
Luis came out and went beyond the minimum and did additional insulation and and reconfigurations of essential elements of the system. Thank You.
Bill - East Fallowfield Township, PA
They did a great job troubleshooting for possible future problems
Bill - East Fallowfield Township, PA
Routine check but all went well, as expected.
Neal - East Fallowfield Township, PA
Great job. Personable and enthused professional.
Great Service! Always on time!
Leigh - East Fallowfield Township, PA
Carolyn - East Fallowfield Township, PA
Bryan was very professional and thorough.
Kitchen mini split joe operating correctly, found system off upon arrival set controller to call for ac at the lowest levels, noticed frost starting to for, on gas line, system is low on refrigerant, leak search is needed to find where the system is leaking then we can provide estimates for Repair
Performed two ac tune ups attic and basement unit, replaced both filters, flushed drain and test pump ok attic unit has no drain protection other than float switch on auxiliary pan, informed customer about it, also showed him the condition of indoor coil, lot of corrosion, check split ok outdoor units refrigerant pressures capacitor and contactor ok, first floor checked out ok on second floor ac found compressor did not start after couple minutes, customer is aware of issue, due to age would recommend replacement of second floor system
Performed ac tune up check electrical low and high ok replace air filter, flushed drain ok check temperature split, blower cap ok, outdoor unit refrigerant pressures r22 ok capacitor and contactor ok, informed customer about system age And currently is working little harder to keep up with load, would recommend start thinking on system replacement
Check system set up, customer is interesting on upgrading the thermostat to WiFi stat, check wires at the thermostat, oil furnace and outdoor unit, provided options to customer customer ok price on T6 pro WiFi stat set up programming on stat to heat pump two stage with oil back up locked out back up heat at 40 and compressor at 35 per customer with 2 degree temp dropped cycle system ok would recommend having oil furnace cleaned /tune up
Found contacter pitted at outdoor a/c. Replaced 40 amp single pole contactor and tested. Also performed precision a/c tune up on Lennox a/c system. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. System is working fine at time of inspection.
Performed ac tune up check electrical low and high ok replace air filter flushed drain add tabs, check split check blower and blower cap, blower housing is very dirty and cap is reading below ratings, also found secondary drain box from heater leaking, showed customer the condition, check outdoor unit refrigerant reassures cap and contactor ok cycle unit emailed proposal for repairs, bill to come out Monday morning to provide estimate for new furnace
Customer concern: heat cycles on and off Upon arrival called for heat and observed furnace. Furnace started in 1st stage and then second but never turned off. I turned switch off and then tried again but furnace did not turn off again. I then proceeded to eliminate possible causes. Cleaned flame sensor. Tightened electrical connections. Checked gas pressures and tested combustion. Everything checks out fine. Air filter needs to be replaced but customer will do herself. Temp rise 55. Informed customer about reme special and included special price estimate while supplies last.
Performed peco heat pump tune up. Replaced 16x25x1 air filter. Checked all electrical conections and components. Found condensation vinyl hose is ran to outside of home. Gave estimate to run vinyl hose to inside to prevent freezing. Also suggested getting a membership for discount on repairs and to perform heat tune up on gas furnace. Heat pump is 48,000 btuâ€™s. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of inspection.
Found weak capacitor. Replaced 15 mf capacitor. Also found dirty air filter. And a lot of junk in condensate tubing. Suggested we do a tune up on the gas furnace. Performed a precision heat tune up on trane gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of service.
Extended exhaust pipe all the way passed deck, and insulated also cutback intake, during same visit eliminated discharge line going outside and attached discharge line to drain inside the house, this will eliminate any potential from freezing during very cold times, test and cycle condensation pump and working ok
Performed gas propane furnace check up, check electrical low and high ok replace filter, check manifold gas pressures low and high ok, combustion test cycle furnace ok clean flame sensor, check venting and found exhaust vent is not insulated and terminates under the deck we need to extend exhaust all the way out and insulate , (2)45 three inch is needed and also foam insulation for 3 in pipe
Performed precision heat tune up on Lennox heat pump. Replaced 20x20x1 air filter. Checked all electrical conections and components. Serviced Aprilaire humidifier with #35 humidifier pad. Checked operation of emergency heat. Found humidistat reading 46% humidity. Put humidifier into test mode and humidifier ran fine. Explained to homeowner that as warm as a winter we have been having humidifier will not cycle as much due to less heating run cycles. Turned up humidistat to highest setting. Checked refrigerant pressures and defrost mode. Did hear compressor change in an audible sound while running, this is wear and tear with age of compressor. Let Neal know that the compressor could stop all together or it could run like this for a while. He is going to see how it goes at this point.
Injected a/c renew into Lennox heat pump, and checked refrigerant pressures. They were 205/47 r22 pressures. With a subcooling of 17.9 degrees. De energized And re- energized the reversing valve to work the ac/ renew thru the system. Heat pump is working fine at time of service.
Performed precision heat tune on Lennox gas furnace. Replaced 16x25x1 air filter. Checked gas pressure. Performed combustion test. Checked all electrical conections and components. Gas furnace is working fine at time of service.
Performed heat tune up, during visit customer informed heat would not come on during last weekend, found open igniter, replace igniter noticed control board always sending 120 volts to igniter during call for heat, thatâ€™s the cause why igniter went, quoted for new board and also upgraded to 120 volts igniter, customer ok with repair, installed new board and 120 igniter, clean sensor and check gas pressures ok combustion test cycle heater ok furnace running ok Now,
Performed precision heat tune up on Payne gas furnace. Homeowner to replace 14x14x1 air filter and 20x20x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Adjusted gas pressures and performed combustion test. Also found 2to3â€ reducer installed incorrectly, recommended changing fittings. Gas furnace is working fine at time of service. Found 2x3â€ reducer horizontally installed and is a water trap
Performed precision heat tune up on Lennox gas furnace. 16x25x1 air filter is clean. Blew out condensate drain. Checked all electrical conections and components. Checked gas pressure. Performed combustion test. Also cleaned flame sensor. Found thermostat is not working correctly and needs replaced, homeowner to replace at this time. Lennox gas furnace is working fine at time of service.
Water leak coming from ac indoor coil, inspect drain and flushed drain ok, no problem with drain, check filter ok check refrigerant pressures, customer had compressor replaced this summer and was converted to R438A refrigerant slightly different pressure differential, new compressor is rated at 45 degree coil temp, check super heat and subccoling 200/55 with 30 superheat and 11 subccoling calculated target superheat, target is 12 with outdoor temp and indoor wetbul temperature relation, system is low in refrigerant
Performed ac check up check electrical low and high ok check filter split ok, check outdoor unit r22 pressures contactor and capacitor ok sub cooling and super heat ok cycle unit ok
Found carrier ac slightly low on charge added 1 lb 10 oz of r 410a. Now have a subcooling of 14.6 unit called for 14 system has a slight leak. System is an 03. Told homeowner they need to start thinking about replacing,they are going to wait at this point. Also performed precision ac tune up on carrier ac. Replaced 20x22x1 air filter. Blew out condensate drain and cleaned pump. Checked all electrical conections and components.checked refrigerant pressures and temperatures at indoor and outdoor units.
Performed ac check up, check electrical low and high ok found blower cap reading 6 rated at 7.5 filter ok flushed drain noticed ac drain slope is not away from coil, primary pan is full of water, causing high humidity and potential for mold, recommend repairing drain line, by installing an ez trap, check outdoor unit 410 pressures ok capacitor and contactor ok cycle unit ok quoted to replace drain trap and correct problem with slope, customer ok with price customer does not want blower cap replace
Performed precision ac tune up on lennox ac. Found clean 16x25x1 air filter. Also found that thermostat switch on older Aprilaire thermostat is going bad and no always switching correctly, recommended replacing with Honeywell t4 programable thermostat. Homeowner is going to let husband know about issue. Also found mouse nest in outdoor unit cleared out and found no wires chewed at this time but could happen in the future. Checked all other electrical components and connections. Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Performed Precision AC Tune Up on Second Floor Lennox Heat Pump System. Replaced 14x24x1 Air Filter, Cleaned EZ Trap on Drain Line. Inspected Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge and found System was low on Refrigerant. Subcooling was at 3 Degrees and Superheat was at 66 Degrees. Added 3 lbs of 410-A Refrigerant to System. After adding Refrigerant found Subcooling increased to 11 Degrees and the High Side Pressures increased. The Low Side Pressures did not change and Superheat remained around 60 Degrees. The TXV in the Air Handler is restricted and not allowing the Refrigerant to flow properly. Need to replace TXV and retest System. System may need additional Refrigerant after the TXV has been replaced. No Dye was added to the system at this time due to issue with the TXV. Do not recommend operating system until repair can be performed.
No ac found indoor blower comes on but no outdoor unit, found open capacitor 60x10 quoted for repairs, once new Calais in we would check pressures and electrical amp draw on motor and compressor customer will pay repairs and then he would get reimburse from warranty company also during same visit check r22 pressures 230/80 inside temp is 78 outdoor temp is 79
Performed ac check up, check electrical low and high, replace filter, flushed drain ok, check split only getting 12, check outdoor unit r22, unit is low on r22, also super boost overheating, and contactor making noise, quoted for repairs and also to add r22 would not recommend doing repairs, system to be upgrade chuck to come out to price complete system