When you need air conditioning, heating and water heater services in Exton, PA, you need DiBiase Heating & Cooling Company. We’ve earned a reputation over the years for providing customer-first service you can count on.
We live by rock-solid values of integrity, honesty and quality. Read our reviews and find out why your neighbors think of our trusty frog mascot whenever they need local heating, air conditioning and water heater services in Exton, PA.
for Exton, PA
Our Reviews by City
Job well done.
Barbara - Exton, PA
Karla - Exton, PA
Great service! Always profesional
Shelley - Exton, PA
Another great visit.
Virginia - Exton, PA
Chris came to service our new heat pump for the summer months. He gave the same professional care as the installers; answering questions and providing helpful tips. A pleasure to deal with DiBiase.
Virginia - Exton, PA
Mike and Paul did a great install of a heat pump while correcting errors from a previous job, while explaining it to me. They were polite, professional, prompt.
Wonderful team, reliable service, and reasonable/fair pricing
Tony - Exton, PA
The DiBiase Team is very responsive, and continually provides excellent - professional services. I would continue to highly recommend their services to others, as I have done. Tony - Realtor/Residential property owner (multiple properties)
Neal - Exton, PA
Great Service, Great Team
Angie - Exton, PA
Craig - Exton, PA
Fast response and courteous staff assisting us with hot water problem.
Craig - Exton, PA
On time... courteous... professional...
DanVer - Exton, PA
Very professional company, Chris was polite and knowledgeable, answered all of our questions, and provided high quality service.
Toni - Exton, PA
Great experience. Efficient, prompt, friendly and flexible with timing. Chris did a great job and fixed my humidifier in an hour when two other technicians (from different companies) were unable to do so.
Great service.....as always from the DiBiase team.
Tony - Exton, PA
good professionalism, responsiveness and timeliness, and completeness also. Courtesy and respectful as well. Luis was wonderful. Thank you, Tony - happy customer
Herman - Exton, PA
I called in the morning to describe an AC problem and they set up an appointment ..... they arrived ahead of time and were very professional. Problem solved, plus they gave me a quote for a new system, which I requested, during the same visit.
Service, Timeliness, Results
Tony - Exton, PA
Most professional service provided; right-on-time; courtesy and completeness. Can't say enough positive things about Joe DiBiase and his HVAC team of professionals. Very customer oriented - shame there are not more businesses functioning like they do! Tony
HVAC and Hot Water Heater Replacement
Diane - Exton, PA
I have been a long time customer and I trust Joe and his team 100%. They are very professional, kind, and technically skilled. I highly recommend them!
Jennifer - Exton, PA
I know I am in good hands with DiBiase. Nathan is one of the best and takes deep pride in his work. I highly recommend DiBiase for your HVAC needs.
Ok service, ok associate
Angie - Exton, PA
everyone I've talked with or worked with previously was great. This particular associate needs a little refresher in customer service. When asked exactly what service(s) he'd be performing as part of the check up, he looked shocked as if he'd never been asked that before then struggled to find the words. When at the end he indicated a part was needed and I asked what the part was and what the issue was, he actually said "how do I explain this". I'm well educated son, I'm pretty sure if you use English and explain it at a laymen's terms, I'll be able to understand.
Great Service, Great Team
Angie - Exton, PA
I lost my air on what felt like the hottest day of the year. Within 1 hour, I made the call, Bryan arrived, diagnosed the problem and resolved it. Great service and Bryan was so nice to work with.
regular service call
Holly - Exton, PA
Great service by Bryan, but the news (cost) was not a good experience, perse.
Tony - Exton, PA
Have never been disappointed with this company. Call and your problem can be solved within a day.
Kathy - Exton, PA
the best service ever
Deb - Exton, PA
very sweet guy great job and very honest!!!!
Kevin - Exton, PA
Arrived on time and was complete on no time.
Steve - Exton, PA
Its always a pleasure dealing with DiBiase, they have come through in heat outage and are right on top of my annual service, pleasant and Knowledgeable service techs.
Talked to Lynn at the holiday inn and found that they were getting a smell from the boiler room . Plumber just installed a new boiler next to the older boiler that share a common vent. They only get the smell when running the new water heater. There plumber is going to come back to find out the smell issue. While we were here we found no exhaust fan in mechanical room duct to outside someone had removed it at some point. Dimensions were 11 1/4 long by 14â€ wide by 11 1/4 high. Checked no cooling on rtu that cools the halls, found low voltage breaker tripped. Reset, found no shorts or grounds. Never got call from thermostat, thermostat stuck in time delay. Jumped out thermostat and air conditioner came on and ran. Need to replace thermostat. Replaced thermostat, started air conditioner cycled and checked operation.Need to add rtu to maintenance plan will need 14x25x1 and (2)15x20x1 filters and a 4l-380 belt Did not email
Checked no cooling complaint, checked air filter ok, checked outdoor unit, found open dual run capacitor. Replaced dual run capacitor. Started air conditioner, checked refrigerant charge, found system low on charge. Recommend replacing due to age 18 years old.
Performed cooling maintenance, checked air filter ok. Inspected cooling coil. Cleaned condensate drain and pump. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge, found getting low on charge. Checked operation and temperature drop across coil.
Upon arrival found the Outdoor Unit was operating but the Blower Motor was not running. Checked Voltage to the unit. The Contactor was not receiving 24Volts for the Coil to engage the Contactor and pass the High Voltage to the Blower. Performed Multiple diagnostics on system and while testing system, it was working intermittently between the running in Heat Mode and not shutting off. Removed the Thermostat wires and reinstalled at the Air Handler. System was operating in Cooling Mode. We will follow up for a return visit to retest System and ensure it is running properly.
Performed Precision AC Tune Up on both Systems for the building. Changed all Air Filters. The Drive Belt for the Second Unit above the Gym Area was very dried and cracking. Replaced with a new V-Belt. Cleaned Condensation Drain Lines from Access points. Inspected and tested Electrical Components on the Indoor and Outdoor Units. Measured Refrigerant Charge on both Systems and measured Supply and Return Air Temperatures.
First floor unit not working, blower works, but no outdoor, found open/blown cap quoted for repairs, recommended replacing system Joe to call customer about pricing and availability for installation
Replace outdoor control board and fan motor. Removed failing control board, installed new control board, wired board. Removed fan motor, installed new fan motor, wired fan motor, powered up air conditioner, cycled thru low and high speed cooling,Warranty no charge
Performed Quality Assurance Inspection on the two Amana Gas Furnace/AC installs. Spoke with customer about concerns with AirFlow. Completed Checklist Form in System. Reviewed installations with Homeowner.
Performed cooling maintenance, checked air filter ok. Inspected cooling coil, blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil. Flushed Navien water heater with flush solution to remove mineral deposits that have built up on heat exchangers or 20 minutes. Flushed with clean water. Started water heater. Cycled and checked operation and water temperature.
Checked no cooling and the thermostat is blank checked furnace found no power to the furnace, found emergency switch off. Turned on, waited for time delay. Started air conditioner, checked operation and temperature drop across coil.
Upon arrival found unit running, quoted to defrost coil and empty secondary pan, cleaned washable filter, filter was clogged, after cleaning and checking pressures system is doing just fine, 410 pressures ok 260/120 with 9 sub cooling and 11 super heat supply temp 49 return temperature is 69,,,,,,20 degree split, com at 1200 com 3 ton outdoor recommended checking/cleaning filter every 30 days
Checked no cooling complaint, found blower running and filter clean, checked outdoor, found power to heat pump but not running. Checked dual run capacitor, found open. Replaced dual run capacitor. Started heat pump, checked refrigerant charge and temperature drop across coil.Maintenance plan $189.00 per year no overtime rates, 15% disconnect on repairs and service.
Performed precision ac tune up on Rheem ac. Replaced 16x25x1 air filter . Blew out condensate drain and tested with water. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Also looked at water heater. Cracked hose drain and checked for sediment, no sediment coming out, possible bad element and or thermostat, due to age recommend replacing water heater. Office to call and follow up with landlord.
When I arrived system was locked out on high pressure cut out. Went outside to outdoor unit , pulled of high pressure switch from board and checked with ohm meter. Wiggled wires while ohm meter was connected circuit stayed closed. Reset power and started up ac and checked 410a pressures at 82 degrees they were 305/135 in second stage. Called amana tech support case # 1223285. Went over issue of high pressure lock out with them to check for any possible issue that has been recorded on hpco. No issues in the system also checked electrical conections to fan motor all intact. Restarted system several times no issues starting. Will go over findings further with office to proceed from here.
Checked heat pump locking out, found outdoor unit locked out on high pressure. Reset lockout, compressor started and the outdoor fan only rocked but never started, high pressure only reached 275. Checked high pressure switch found closed. Reset lockout, compressor and fan started. Checked for shorts in high pressure wiring. Found where the wires pass thru the cabinet the wires are getting pinched. Freed up wire harness to allow room without pinching wires. Cycled heat pump, checked operation and temperature drop across coil.
No ac, found blower running but not compressor, found blown capacitor, test unit with new one, compressor would not added hard start assist unit came on, run unit for 10 mins check preesures 190/75 liquid line temp 88 suction line temp 74 running at 34 super heat and 12 subccoling position meter device target super heat is 24, quoted for necessary repairs customer wast to hold on refrigerant, supply air 60return air 86
2nd floorReclaimed and removed old equipment. Installed new pad with stone and whip. Flushed lineset. Set new Amana condenser. Brazed in condenser and wired. Installed new gas furnace and evaporator. Brazed in evaporator and pressure tested to 300. evacuated lineset down to 278 microns. Reconnected electric and gas. Leak checked lineset and gas. No leaks found at time of install. Installed ez trap and condensate pump and tested. Replaced flu pipe up to b pipe. Cut in new filter rack. Tested system and adjusted charge as necessary. Everything working great at time of install. 16/25/11st floor Reclaimed and removed old equipment. Installed new pad with stone and whip. Flushed lineset. Set new Amana condenser. Brazed in condenser and wired. Installed new gas furnace and evaporator. Brazed in evaporator and pressure tested to 300. evacuated lineset down to 265 microns. Reconnected electric and gas. Leak checked lineset and gas. No leaks found at time of install. Installed ez trap and
Performed quality 6 month check, replaced standard air filter. Checked leak at eztrap. Brushed out trap itâ€™s clean. Tested with water, filled trap found no leak. Started air conditioner, checked for air leaks ok. Checked refrigerant charge, topped off charge, balanced by sub cooling. Checked operation and temperature drop across coil.
replaced blower motor and added surge protector and cleaned blower wheel. After replacing motor found that the 24 volt molex wiring harness is very brittle from age and wires are coming loose from harness had to electrical tape to keep wires in, recommended we replace harness also. Called johnstone supply for price and availability. Everything is back up and working at this point, need to replace harness to keep motor running. Manager okey wiring harness replacement. Ordered from johnstone.7/16/19 replaced blower wiring harness and checked delta t it was 19 degrees very good. Checked pressures they were 325/128 410a . (Talked to Lynn about office, seem to just be getting warmer front the old wiring harness not always making conection should work fine now)
Checked no cooling, started air conditioner, started air conditioner, found blower not starting, found new thermostat not set up with air handler. Set up and ran air conditioner, found outdoor disconnect pulled. Plugged in and compressor started and off on internal over load. Checked run capacitor ok. Found start capacitor failed replaced with spp6 start assist. Started air conditioner, checked refrigerant charge.
Installed a new air conditioning unit under warrant changed lineset insulation outside and re caulked penetration. Cleaned off the whip and disconnect evacuated system to 187 microns and held after triple evacuation. Added 2ounces of charge.
Performed cooling maintenance, replaced standard air filter, inspected cooling coil, blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started heat pump, checked refrigerant charge and temperature drop across coil
Found outdoor heat pump kicking on but not ecm blower motor. Found 24 v between common and green going to control board. Bad ecm motor. They had just recently had the power kick on and off so this possibly took out them motor. Called the distributer for price and availability. Need to have motor shipped to the shop. Also will install surge protector and clean blower wheel. Got repair approved ordered motor. Ordered from Lyon Conklin.
Service call to provide estimate for Air Flow Issues in the Home. Spoke with Homeowner about options for Zoning or Air Balancing. Counted 24 Supply Runs on System. Also spoke about cleaning/flushing Service of the Tankless Water Heater. Need to follow up with Customer with estimates for Zoning, Sealing Ductwork, Servicing the Tankless Water Heater, and Service Membership.
Performed cooling maintenance, replaced standard air filter. Checked condensate drain and pump. Inspected cooling coil. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil. Checked blower running when fan is in auto and system off. Found all wiring ok. Cycled blower and air conditioner. All starts and stops as switched. Found nothing wrong.