DiBiase Heating & Cooling Company proudly serves our neighbors in Folsom, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience.
We do this by providing the fastest services from the most qualified technicians in the Folsom, PA area. See what your neighbors are saying about our unshakable customer-first service!
for Folsom, PA
Our Reviews by City
Linda - Folsom, PA
Chris is friendly and courteous. Willing to answer any questions I had. Explained everything he did.
Linda - Folsom, PA
Chris is very courteous and answered all my questions. Even though he arrived later in the day, but within the time I was told, he was very thorough and found the reason for me not having heat.
Performed Precision Heating Tune Up on the Gas Fired Boiler. Removed Burners and Cleaned. Cleaned Pilot Assembly and Thermocouple. Inspected Heat Exchanger while Burners were removed. Cleaned Pressure Switch Tubing. Put Boiler in operation to test. Tested the Expansion Tank and found that it was full of Water. Recommend Draining Expansion Tank of Water. The Expansion Tank helps protect the Boiler and the Piping in the event of an influx or increase in Water Pressure. Included an estimate for the Draining of the Expansion Tank. Tested Water Temperature and Water Pressure. Performed Combustion Analysis on Boiler.Performed Heating Tune Ups on the Mini Split system with Three Indoor Units. Removed and cleaned Air Filters and Indoor Coils on each unit. Tested operation of Units in Heating Mode. Inspected Components on Outdoor Unit and tested for proper operation. Supply/Return Air Temperatures on each system were to standards. Showed Homeowner how to remove the Air Filters on the Units t
Service call that the Gas Fired Boiler was not operating. Arrived onsite and spoke with Homeowner about issue. Found that the Pilot was lit but the Boiler would not Fire off. After troubleshooting system, found that the Pressure Switch was not gettng the correct amount of pressure to close and open the Gas Valve. After further troubleshooting determined that the Flue Pipe was clogged. Removed Flue Pipe and found a Birds nest in the Vent Pipe. Cleaned Vent Pipe and reassembled. Resealed the Vent Pipe with High Heat Silicone and Metal Tape. Put Boiler in operation and performed Combustion Analysis.The office will call to schedule a return visit to perform Heating Tune Up on Mini Split System and the Gas Boiler.