DiBiase Heating & Cooling Company proudly serves our neighbors in Garnet Valley, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience.
We do this by providing the fastest services from the most qualified technicians in the Garnet Valley, PA area. See what your neighbors are saying about our unshakable customer-first service!
for Garnet Valley, PA
Our Reviews by City
Good tech well trained
Mike - Garnet Valley, PA
Upon arrival found unit low on charge. Added refrigerant to bring to standards. Put dye into system. System only 3-4 yrs old. Supply temp 48 , low 117 high317 sh 9.7 sc3.8
Performed precision air conditioning Tune Up. Cleaned Washable Filter. Turned Humidistat to the Off Position and Closed Dampers on the Humidifier for the season. Placed Outdoor Sensor in a proper position on the Outdoor unit as it was exposed to the sunlight. This will give accurate outdoor temperature readings for the system to work efficiently.Based on Pressure/Temperature readings, the system is low on refrigerant. While it is maintaining sufficient temperature splits, the lack of refrigerant will not only lower the cooling efficiency over a prolonged amount of time during hot days, it will damage the compressor as it requires refrigerant gases to cool down during heavy operations. We recommend Charging 3 lbs of R22 into the system as a temporary solution. Best option would be to replace the 14 year old system.Added First 2lbs of R-22 Refrigerant using Superheat/Subcooling Charging Methods. Originally quoted 3 lbs of Refrigerant, but the additional 3rd Pound was not needed. Offi
Down in Garnet Valley finishing up a Heat Tune Up on a Lennox Gas Furnace. Some comfort features that this system has include Electronic Air Filter, Humidifier, and Zoning for the First and Second Floors. Check out that sweet Hot Water Heater! We installed that several months ago over the summer.
Installing a new 50 Gallon Bradford White Natural Gas Hot Water Heater in Garnet Valley. We installed a Flood-Stop Valve, new Expansion Tank, and a Pan with this Hot Water Heater. We are waiting for the Water Heater to finish filling before we turn it on.