When it comes to your Glenmoore, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Glenmoore, PA to see how we live up to these values every day, in every way.
for Glenmoore, PA
Our Reviews by City
Courteous and Thorough
Jeanne - Glenmoore, PA
Lisa - Glenmoore, PA
Charlie - Glenmoore, PA
Kurt did an excellent job. Efficient yet thorough. Would be happy to have him again.
Amba - Glenmoore, PA
Top Notch Customer Service
Sandy - Glenmoore, PA
They truly care that you are more than 100% Satisfied and do quality work! Companies like DiBaise are getting harder and harder to come by. They stand behind you and their work!
Great, timely service. 😄
Kathleen - Glenmoore, PA
Rose - Glenmoore, PA
Rose - Glenmoore, PA
Nate is great!
John - Glenmoore, PA
Nathan is highly competent, thorough, and honest. As long as he’s on our account, we’re a customer!
Business as Usual
John - Glenmoore, PA
Nate always does a great job for us!
Found oil strainer un -cleanable. Replaced oil strainer and performed precision heat tune up. Replaced rf1 oil filter. Replaced 1.00 80a nozzle. Performed combustion test. Oil furnace is working fine at time of service.
Survey for dehumidifier and humidifier, found 2 systems first floor and second floor. Also has a sump pit with no pump installed. There is a new sump pump that needs to be installed. Would need to install pump into pit and run 2â€ discharge out of house. See pictures Dehumidifier would be installed on first floor system and humidifier would be installed on second floor system Recommend adding service plan to get discount see estimate.
Upon arrival found burners tripped on primary, reset primary and no flow of oil, noticed air coming from bleed port, purge all air and test burner ok would recommend adding a tiger loop and convert burner into two pipe system to prevent any more air getting into line emailed proposal for repairs customer will think about it
Performed two propane gas heater check ups, check electrical low and high ok replace filter on first floor unit second floor is ok, second floor unit looks ok gas pressure clean sensor and combustion test heater running within manufacturer settings, on first floor heater found heat exchanger rusted more than normal that you would see, heavy rust also igniter has lot of white residue combustion test within good numbers for safety issues would recommend having system replace Customer will take care of humidifiers
Performed precision heat tune up on amana heat pump system. Replaced Aprilaire 313 air filter. Blew out condensate drain. Checked all electrical conections and components. Installed new humidifier filter tray and Aprilaire #35 pad in American standard humidifier ( tray was broken during the recent installation). Tested humidifier operation . Checked refrigerant pressures and temperatures at indoor and outdoor units. System is working fine at time of service.
Performed precision heat tune up on dynatherm oil boiler. Replaced.85/80b nozzle. Replaced rf1 oil filter. Brushed and vacuumed out oil boiler. Performed combustion test . Boiler is working well at time of service.
Basement unit not working properly, upon arrival found system off and temp at 67 check ac operation and found no pressure on outdoor unit, outdoor coil is in bad shape covered with dirt and looks like oil around coil, quoted for repair, due to condition and age would recommend replacing coil and outdoor emailed quote for potential repairs additional cost will be extra once we find the problem,
After talking to homeowner he said that randomly the a/c would kick on and the heat at the same time. Homeowner had a Nest thermostat, possibly the thermostat was causing the malfunction. Recommended we replace it with a Honeywell t4 thermostat. Replaced thermostat and checked r22 pressures they were 200/70 pretty good. Homeowner signed up for maintenance contract. Performed precision heat tune up on York oil furnace. Replaced 16x25x1 air filter. Replaced.65x70 b nozzle. Replaced rf1 oil filter. Checked temperature rise of oil furnace. Furnace is older but running fine at time of service.
Performed quality assurance evaluation on system. All work looked good. Customer very happy with installation.
Performed Quality Assurance On recently installed Daikin Mini Split System. Reviewed Installation and completed Checklist Form in System. Corrected any issues that were found.
Performed Quality Assurance On recently Installed Amana Gas Furnace/Heat Pump System. Corrected issues that needed to be addressed. Reviewed installation with Homeowner. Completed Checklist Form in System.
Performed Quality Assurance On Amana Heat Pump System. Completed Checklist Form in System. PECO # is recorded in the Notes. Reviewed installation with Homeowner. Need to follow up with Homeowners about the Oil Tank and possibly insulating the Plenum.
Performed ac check 6 month inspection washed filter check electrical low And high ok check split Ok check outdoor unit pressures ok capacitor and contactor ok cycle unit ok
Installed a new furnace on feet on existing plastic pad . Installed a new 3 ton coil on top of the furnace and modified duct work as need . Ran new condensate drain with an Ez trap and added a new pump . Drained over to sewer drain. Reconnected existing return duct and changed the filter 20â€x25â€x1â€ filter. Ran new copper lines to the outside 3 ton Ac unit . Ac is on heat pump feet on a new plastic pad. New disconnect box and sealtight on exsisting wire to indoor. Calked and sealed all penetration. Put in a new thermostat prestige iq with eim and outdoor sensor walked threw with customer .
Took out old ac coil and outdoor unit, also removed the old line set and comm. wires going to outdoor unit. Installed new indoor coil on top of existing oil furnace and did metal work to fit it properly. Installed new ez trap and condensate pump with discharge line going into the sewer line. Tested and works properly. Leveled out outdoor area and installed new pad for outdoor unit and ran new line sets and communication wires. Pressure tested lineset to 300, no leaks. Evacuated lineset to 266 microns. Tested all components and is all working as it should.
Replace blower bearing for living room ductless head, test and cycle operation ok
Put batteries in new daikin remote and cycled ductless in both heating and cooling mode, I placed remote on table below indoor unit.
Reclaimed and removed old equipment. Installed new pad, disconnect, lineset, whip, and heat pump on heat pump feet. Brazed in outdoor unit and reconnected electrical. Installed new return box, return duct, and new air handler. Reconnected supply and return ducting. Installed heat kit. Ran new wire for air handler and tied into panel and unit. Installed new ez trap and condensate pump to break r wire. Brazed in air handler and pressure tested to 300. No leaks found. Evacuated down to 145 microns. Removed old oil tank fill and vent lines and closed holes. Removed old oil supply line. Installed new receptacle for condensate pump. Capped old chimny pipe. Ran vinyl into discharge line. Tested system and adjusted charge. Delta t 21 degrees. System working properly at time of install.
Found bearing assembly making noise,, tried to lubricated sounds is lower but still making some sound, called supply house, they will send new assembly takes couple days to get it since they donâ€™t have it in stock, office will get back to customer when part has arrived to schedule repairs
Performed ac check up, oil furnace with ac unit, flushed drain test pump ok, check blower cap ok filter, ok split is only 15, return is 73 supply 57, check outdoor unit found low bare low voltage wires, contactor making buzzing sound, and unit is low in r22, blower wheel is really dirty needs cleaning, quoted for repairs due to condition and repairs recommend replacing system current units is from 1989 bill to come tomorrow around 5 pm for quote on new system
Performed two ac check ups, attic and basement units, check electrical low and high ok replace both filters, 16x24x1 and 20x20x1 flushed drain ok check split, replace blower cap for attic unit, check outdoor units r22 pressures capacitor and contactors ok cycle units ok
Performed precision ac tune up on 2 carrier acs. Filter sizes are both 16x25x4 homeowner to replace. Checked all electrical conections and components. Blew out both condensate drains. Checked refrigerant pressures and temperatures at indoor and outdoor units. Both systems working fine at time of service.
Performed ac check up on heat pump electric heat as back up, check electrical low and high change filter, flushed drain test pump ok check split coils are clean, noticed double pole contactor for electric heat all pitted and burnt contacts, informed customer, also check outdoor unit 410 pressures capacitor and contactor, found cap reading 39 rated at 45/5 cycle unit ok emailed recommended repairs
Upon arrival found unit running but no water leaking, check drain, head is little unleveled reposition drain line and bracket, cycle and test drain, poured gallon of water draining ok
Performed precision ac tune ups on 2 carrier acs. Replace 2 413 air filters homeowner provided. Found no saftey trap on second floor ac, so recommend ez trap. Also found contacter burned and pitted at outdoor unit. Also found capacitor tested week to second floor system, highly recommend repairs. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Systems are both running at time of service.