DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Glenolden, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Glenolden, PA.
for Glenolden, PA
Our Reviews by City
Performed Precision Air Conditioning Tune Up on system. Replaced 16x25x1 Air Filter. Cleaned Condensation Drain Pipe. Inspected Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge and Supply/Return Air Temperatures. System is running to standards.Please note Hot Water Heater is from 3/2008. Average life of Residential Water Heaters is 10-12 Years. Recommend replacement of 40 Gallon Natural Gas Atmospheric Water Heater before any issues occur.
Performed Precision AirmConditioning Tune Up/Inspection on Unit. Replaced the 16x25x1 Air Filter. Tested Electrical Components on the Indoor and Outdoor Units. Measured Refrigerant Charge on system. Refrigerant Levels are running to standards.Performed Precision Heat Tune Up/Inspection on the Gas Furnace. Inspected Heat Exchanger and tested the Integrity of the Heat Exchanger using a Smoke Test. Heat Exchanger passed the Smoke Test. Measured Gas Pressure of Unit while performing Combustion Analysis on Furnace. Furnace is running to standards.Both the Air Conditioner and Gas Furnace are running to Manufacturers Standards. System is old, Manufacturer date is from 1993. While the system is operating to specifications it is not operating as efficiently as a new system. Recommend performing Annual maintenance on the Air Conditioner and Furnace to help maintain the system, and help prevent issues from arising. Also recommend begin planning for replacement of the Gas Furnace/AC.
Installed new Evaporator Coil and new transition from coil to existing metal. Reconnected Drain and Vent Pipe. Installed new Condenser on a new Pad, ran new Lineset, installed new Disconnect and whip to Unit. Ran new line set with new Line Hide at Outside Wall. Start up and test operation and adjusted charge.
Performed Precision Air Conditioning Tune Up on system. Checked Air Filter. Cleaned outdoor unit coil with water due to being full of lint and debris. While testing system, found both the Blower Motor Capacitor and the Dual Capacitor for the Outdoor Unit were testing below recommended rating. Also found Contactor worn and Pitted on the Outdoor Unit. While measuring Refrigerant, found system to be slightly low on refrigerant charge. Temperature Splits were measuring at 17 Degrees and Superheat Levels were higher than recommended. Included is an estimat for the recommended repairs.Due to age of Air Conditioning System, replacement of the Air Conditioning System is recommended. The office will call to schedule an Estimate for Replacement.Visually inspected Hot Water Heater. Water Heater was manufactured in September 2009. Average life of Wtaer Heaters is 10-12 Years.
You never know what surprises lie waiting for you as you take the cover off of a unit! I found this earlier today on a no Heat Call. Apparently the can was supporting the Pilot Tubing which was not fully tightened, and was leaking gas which was creating a small flame underneath of the Pilot Assembly.