DiBiase Heating & Cooling Company proudly serves our neighbors in Haverford, PA with complete heating and air conditioning services. Our goal is provide you with the ultimate customer services experience.
We do this by providing the fastest services from the most qualified technicians in the Haverford, PA area. See what your neighbors are saying about our unshakable customer-first service!
for Haverford, PA
Our Reviews by City
Service call that the Air Conditioning was not working properly. Upon arriving, found Thermostat was set to 63 Degrees and the Temperature within the home was 77 Degrees. Temperature differential was at 10 Degrees. After troubleshooting system, found Compressor was completely frozen and the Indoor Coil was frozen. Defrosted both the Indoor Coil and the Compressor. Put system back in operation and tested Refrigerant. System was low on refrigerant which was causing it to freeze. Added 3lbs of 410-A Refrigerant to system. Monitored system, and charged unit using Superheat Guidelines. Upon completion temperature Split was 18 Degrees. Replaced the 20x20x1 Air Filter. Set Thermostat to 72 Degrees.Performed a quick leak search using the UV Light, and was unable to find a source of the leak at this time. Due to no one being home at this time, the Office will follow up for payment.
Performed ac tune up on 4 systems. Replaced filters on all units in basement. Replaced 2 capacitors on outdoor units.
Performed Precision Heat Tune Up on system. Replaced 20x20x1 Air Filter. Found Blower Compartment and Blower Motor was very dirty and dusty. While testing system, 7.5 Mfd Blower Capacitor was testing below the recommended rating at 6.7 Mfd. Replaced Blower Capacitor and tested operation. Visual inspection of the Hat Exchanger shows that rust is forming. This could compromise the integrity of the Heat Exchanger over time. Performed Smoke Test to check the Heat Exchanger, Smoke Test passed. Tested Combustion Levels of Furnace.Was informed that the Daughters Bedroom and the Sons Bedroom were colder than the other rooms upstairs. Daughters bedroom only has one register. The sons bedroom has two vents, but one of the vents was closed. Need to keep both registers open in the Sons bedroom. Recommend Air Balancing of the system and adjustment of the registers. If Air Balacing and Adjustment of the registers does not work, the next possible solution would be a Duct Booster.Due to age and