When it comes to your Havertown, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Havertown, PA to see how we live up to these values every day, in every way.
for Havertown, PA
Our Reviews by City
Performed Precision AC Tune Up on American Standard System. Replaced 16x25x1 Air Filter. Cleaned Drain Line, EZ Trap, and Pump. Inspected Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge and recorded Supply Return Air Temperatures. System is operating to standards.Due to age of Water Heater (10 Years), would recommend Replacement of the Power-vented Propane Water Heater before any issues arise.Would also recommend installing an ECM Motor Surge Protector onto the Blower Motor. The Motors can be sensitive to Power Spikes/Surges which can cause damage. The one time Surge Protectors May help protect the Motor in a Power Surge Event.
Service call that the Heat was not working. Upon arrival, found the Heat was turned off. The Blower Motor Housing had been removed from the Furnace and was sitting in the bottom of the Furnace Cabinet. Turned the system on and the blower turned on, but was making a loud grinding/squealing noise. This is an indication that the Blower Motor is failing and the is beginning to seize internally. Removed the Blower Motor and installed a new 115V Replacement Blower Motor with a new Capacitor. Wired Motor into system for Heating and Cooling Fan Speeds. Tested operation of system in Heating and Cooling Mode to ensure proper operation of the Blower Motor.
Performed Six Month Inspection on system. Cleaned EZ Trap and Condensation Pump. Inspected all Electrical Components. Replaced the 16x25x1 Air Filter. With System being installed in the summer, tested the Heating Side of the System. Measured Gas Pressure and performed Combustion Analysis on Unit. System is operating to Manufacturer Specifications.Spoke with Homeowner about Water Heater, due to being 9 years old. She would like to replace the Water Heater before Spring next year. At this time there is no water leaking or visible signs of damage to the Water Heater. Their is some corrosion forming at the Base of the Venting Pipe.
Installed new gas furnace and air conditioner. INstalled new Honeywell Pro T6 thermostat. Sealed duct system with mastic. Setup and tested operation.
Performed a maintenance and repaired a moisture issue on a Amana Gas Furnace