When it comes to your Kennett Square, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Kennett Square, PA to see how we live up to these values every day, in every way.
for Kennett Square, PA
Our Reviews by City
Knowledgeable and professionable
Sue - Kennett Square, PA
Bernhard - Kennett Square, PA
Nathan was on time and the text feature is very good. Handled the problem very professionally.
Jim - Kennett Square, PA
Delivered fast, efficient, on-time, and reasonable service. Best investment we made.
Great service on time
Susan - Kennett Square, PA
Consistently Great Service!
Christina - Kennett Square, PA
I've had a service contract with DiBiase for almost 10 years and I can't imagine using a2 anyone else. Nathan came back out today to "tweak" my heating system and showed up within two hours of my calling the office. All of the technicians are professional, efficient and polite.
Colleen - Kennett Square, PA
Nathan arrived timely to assess hot water heater problem. Was scheduled following morning for installation. Nathan explained the problem in layman terms. He was open to questions the morning of installation. He went over the new hot water heater once installed & left my basement as he found it - neat & tidy. DiBiase technician's are informative & friendly. The prices are competitive. I have been a customer for years & have no plans on changing my HVAC company!
Laurel - Kennett Square, PA
The guys were pleasant and completed service under expected time. Showed up on time
Jim - Kennett Square, PA
Great service, neat,efficient and very courteous.
Kelly - Kennett Square, PA
Bryan was on time, respectful and quick at diagnosing the problem and gave us all of the options for fixing it.
Rick C - Kennett Square, PA
Very satisfied with DiBiase Heating and Cooling. Great communication for scheduling and have always arrived on time. Service technicians are courteous and professional.
Great, reliable service
Rick - Kennett Square, PA
Bryan arrived on time, very professional
Very professional, prompt, honest excellent service
Kathy - Kennett Square, PA
I would highly recommend Dibiasi, great people, excellent service
Laurel - Kennett Square, PA
Service guy was very efficient and professional
Happy with service & price!
Colleen - Kennett Square, PA
very good service
Brett - Kennett Square, PA
The excellent service I have come to expect
Neil - Kennett Square, PA
As always, on time and first rate service.
Found no call for heat to furnace from thermostat. Found only RC wired at thermostat and configured for RH and RC wiring. Reconfigured thermostat and tested operation. Sealed around vent at inside and sealed vent pipes outside. Checked all other dipswitches. Tested operation.No charge warranty call back.
Performed gas heat inspection on 8 heaters check electrical low and high ok clean sensor and burners ok, gas pressure ok, combustion test replace filter, all safeties ok, check split ok, system ok customer aware units not having water protection, also unit number one SPA gas valve repairs s delaying on ignition recommend replacing
Performed gas heat inspection, check electrical change filter, clean flame rod, burners ok gas pressures ok, combustion test noticed lot that of wear on igniter not glowing as much, replaced igniter cycle heater ok,
Installed a new amana outdoor unit on a new plastic pad. A new disconnect box and whipwas installed. A new lineset and outdoor wire was ran and tied into the new unit. The hole and around the disconnect box was caulked and sealed. In the basement we installed a new amana gas furnace and amana coil on top of it. We had to cut the existing return box so that the Aprilaire air cleaner adapted to the side and goes into the left side of the gas furnace. A new humidifier was installed where the old one was removed. A new air scrubber UV bulb cleaning device was installed onto the new plenumon top of the coil. The condensate drain is all new from the humidifier and from the new coil. A new EZ trap was installed onto the new condensate line and runs into a new condensate pump. Both the condensate pump and EZ trap are wired to the unit. The vinyl tubing used to go outside. Now it runs along the ceiling and goes into the sump pump pit. A new box with an outlet and switch was installed onto the n
Per customer, there s water around heater, upon arrival no one home, went down to basement and start ac check drain flushed drain ok blower ok, filter ok, noticed very dirty filter next to unit, recently replaced, check outdoor unit 410 ok cleaned condenser coil due to all sides been dirty almost blocking full airflow, coils is clean now, good pressures, most likely problem was a dirty filter ac coil freezing up, then when unit shuts off, coil melts dripping water around heater,
Ac tune up . Checked filter / Clean . Cleaned trap . Tested capacitors on indoor and outdoor units . Checked contator on outdoor unit . Checked all low and high voltage readings and wiring. Tested air temperature splits and refrigerant charge. Tested overall system and system is running to standards .
No ac found system low on charge ( r22 ) and the indoor filter was dirty . Replaced filter and added 2lbs of r22 to the system . Tested overall system and system is running to standards with a temperature split of 18 degrees. Supply 61 Return 79
Zone damper fell off . I reattached the damper motor and tested out . Damper is working to standards.
Performed ac tune up. System is running to manufacture specifications at this time.
We will install an air scrubber in the supply air duct and complete all wiring connections. Installed air scrubber and tested out .
Drain, disconnect, and dispose of old water heater,Install new water heater approximately 8" over to the left in a new drain pan and install water alarm.Install new expansion tank.After I Filled, purged, and tested operations the water heater is running to standards.Ac tune up . Changed filter . Cleaned pump and trap . Tested capacitor on outdoor unit . Checked contator . Checked all low and high voltage readings and wiring. Tested air temperature splits and refrigerant charge. Tested overall system and system is running to standards.
Completed install and tested operations. Filled out form .
Upon arrival found system low on charge. 14 yr old Lennox unit.Recommend replacement due to age and conditionJoe is going to call to come out and provide estimate to replaceCurrently no ac
Found unit running on arrival and second floor reading 72 and set at 72, 1st floor set at 72 and reading 72, basement turned off and at 64 degf, loft set at 70 and reading 79. Condensate present in mechanical room. Dried off all condensation on ductwork. Found supply air temperature at 42 degf. Found fan speed at 700 for 1st stage cooling and 1100 for 2nd stage cooling. Adjusted airflow settings to 800 cfm for low and 1200 cfm for high stage. Disabled loft thermostat at wireless module and zone panel so system would not try and run when all dampers are in closed position. Loft damper is set at position 3 to get airflow always moving at the loft. Set 2nd stage cooling to run after 5 minutes run time to ensure airflow would get to upper levels. After adjustments were made supply air temperature stayed at 52 degf with just 2nd floor zone turned on. Tested all zones for proper operation. Set lockout temperature at zone panel to 40 degf. Checked airflow to basement zone to ensu
Reviewed system. Measured delta accross coil, checked fan speed settings (high). Measured refrigerant charge after home warranty company charged unit. Suction 72/ liquid 275 / SH 8 / SC 8. Delta accross coil is 16 degf. Sat low side is 42 and high side is 124.
Upon arrival duct work sweating and not kicking into second stage causing extreme cold temps. Also basement was cold an drew eac floor after got warmer and warmer.Adjusted settings in zone panel. Wired zone 4 damper to zone 2. Closed bypass partly in hopes to push more air to upper levels, and bring air temps higher to stop the sweating.
Service call that the Air Conditioner was not cooling the home properly. Arrived onsite and spoke with the Homeowner about issue. Found the 1st Floor, 2nd Floor, and Loft were calling for Cooling but were not reaching the set point. Air Conditioner was on, with all Thermostats/Zones except the basement calling for cooling. No Fault codes were being displayed. There was a large amount of Condensation on all of the Supply Ducts in the basement around the unit. After inspecting system, found the Powerhead for Zone 1 was loose and was not opening/closing the Damper properly. Tested Damper and secured Powerhead to the Damper. Tested Damper multiple times. Checked Fan Speed Settings, and Increased settings to Profile B, with a +10% Trim. Changed 16x25x1 Air Filter which was dirty. Put system back in operation.We will follow up in the next 24-48 Hours to see how the system is operating.
Performed ac tune up. System is running to manufacture specifications. Changed filter 16/25/1Could not clean condensate line. No access
Replaced second floor zone dampers and tested operation.
Performed precision ac tune up. System is running to manufacture specifications . Filter 20/25/1 new.
Service call that the Mini Split System was not cooling properly. Arrived onsite and spoke with Owner about issue. Inspected the two Mini Split Heads. Air Filters were dusty but not heavily soiled. Removed Filters and Cleaned. Attempted to clean Indoor Coils with vacuum. Indoor Coils have dirt and lint caked on them. Reassembled the Heads and put back in operation. Took temperature Splits on both Heads. The Head above the Vending Machines was producing about a 20 Degree Supply Versus Return Temperature. The Head above the Dryers was producing between 20-30 Degree differential. The Outdoor Unit would run for about 10 minutes and then shut down for 60-120 Seconds before restarting.Spoke with technical support from LG. Measured Refrigerant Charge on system. Suction pressure was at normal range, but the Head Pressure was elevated, ranging between 400 - 450 PSIG. Checked Voltage on system, and DC Voltage on the Communication Wires. All Voltages were at normal ratings. Units are not produ
Responded to an AC tune up. Customer thought system was low on charge. I found two zone dampers on the second zone to be faulty. And wasn't allowing the air to go to that part of the home. System is running to factory standards aside from the faulty zone dampers. Recommend getting the zone dampers replaced ASAP.Zone dampers are 12X8 (12in long X 8in High)
No AC . When I arrived the system was running . I checked the amp draw on the contactor for the outdoor unit and I was getting 1.9 amps . I found the compressor not running but the outdoor fan was . I shut the outdoor unit down by pulling the outdoor disconnect . I checked all high and low voltage connections. I then started the outdoor unit up and tested amp draws again . The system came on and I was getting a amp draw of 11.17 . The compressor and fan motor was running . I checked the contactor. / good . I then cycled the power on the outdoor again to find the compressor would not start back up . The only thing that was running was the outdoor fan motor . I then waited for about 2 minutes then cycled the power again and the system ran and so did the compressor. While the system was running the temperature splits were 16 . Return 66 Supply 50. I took the temperature of the breaker and the temperature was 78.6 degrees . After testing the system out I feel the compressor could be failin
Performed ac tune up. Indoor capacitor is below rating. Thermostats keep going offline due to wiring issue. Outdoor coil was cleaned but pressures are still high along with superheat, refrigerant a little low but if added will not solve issue and financially not worth. Adding refrigerant will also bring pressures higher. Replaced filter 16/25/1.Recommend replacing system due to age and condition.
Performed ac tune up. Changed filter 16/25/1. System is running to manufacture specifications.Added union for condensate cleanout.