When it comes to your Malvern, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Malvern, PA to see how we live up to these values every day, in every way.
for Malvern, PA
Our Reviews by City
Great service, reliable, professional
Eileen - Malvern, PA
Stephanie - Malvern, PA
DiBiase always comes through when I need them. Nice service guys and reasonable prices. I recommend them to everyone I know!
Brian comes to the rescue
Nancy - Malvern, PA
Brain came out in a very hot day to get the A/C working. He also gave us some great information on replacement units that we may consider.
Chris was great on our service for summer checkup- very thorough , he explained our system well, and made adjustments as we needed.!
Gerald - Malvern, PA
Tai - Malvern, PA
DIbiase always has good knowledgeable technicians
Kay - Malvern, PA
Excellent Service! Christopher is great!
Albert - Malvern, PA
I have always been thrilled with your company's service. Christopher is very knowledgeable, communicates in ways that are easily understood, and is a fine person.
Quick and quality service
Kelly - Malvern, PA
The team who installed my central air was efficient and focused on the job. They were thorough in their work and very pleasant to have during the service!
Joe - Malvern, PA
Thanks for great service
Joe - Malvern, PA
Bryan is TERRIFIC!!!
Vicki - Malvern, PA
Bryan is on-time, patient in handling our "20 questions", explains things clearly, great sense of humor, great ambassador for the company.
Exactly what you hope for
Tom - Malvern, PA
They are on time (actually early) but communicate with you. Do what they need to, do it quickly and correctly.
Friendly, Professional Service!
Barbara - Malvern, PA
We have been very happy with your service as well as the knowledgeable technicians. Bryan was so courteous. Our only regret is that you don't do plumbing work.
Great sevice. Very professional.
Mike - Malvern, PA
Exceeded my expectations
Tom - Malvern, PA
Found water stain on top of exsisting gas furnace with no current water leak, the stain is from the previous a/c coil before new coil was installed. Also found hallway thermostat keeping on fan at other 2nd floor zone system. Homeowner needs both furnaces tuned up beacause off selling house. Will return and install new t4 thermostat.
Recently new install per install team outdoor fan not working, check operation getting 24 volts and also 245 fan is working no issues found, Performed quality assurance during same visit had to tighten outdoor valve caps and also on furnace drain vent make sure was not double trap affecting performance
Checked no heat complaint, found no call from thermostat, found failed thermostat. Replaced with Honeywell t4 thermostat, set up thermostat, have call for heat but the relay on the control center is missing. Installed new relay. Heat now operates. Performed heating maintenance, cleaned burners and pilot burner. Inspected heat exchanger. Checked voltage, amperage and electrical connections, checked water level. Started steam boiler, measured fuel pressures and adjusted manifold pressure. Tested limit and safety switches. Checked operation and temperature.
Installed a new American standard furnace in existing Location. Installed a new coil n top of furnace and adapted
Checked no heat complaint, set thermostat to heat, outdoor starts and runs but not heat, checked outdoor unit, shifted to cooling, cooling pressures are ok, set back to heat, low side pumps down and head climbs. Have a failed outdoor txv.Need outdoor txv for Rheem RP1424AJINADid not email
Performed two gas heat check ups check electrical low and high ok clean sensor and check burners ok gas pressures ok combustion test and test pumps temp split ok replace both filters ok also test humidifier set to winter 35% cycle both units ok
Performed heat pump tune up. Checked electric heat kit. Inspected all electrical components and connections. Checked temperature rise. Changed air filter. Blew out condensate. Inspected coil. Taped up lineset. Checked refrigerant charge and discharge temperature. Tested capacitor. System is running well at time of service.
Performed oil furnace cleaning, check electrical low and high ok replace air filter, clean heat exchanger and flue pipe ok replace oil filter, and nozzle, had to replace strainer completely blocking oil flow, check pump pressure and coupler ok readjust electrodes and check integrity ok performed smoke test adjust air ratio and also performed combustion test cycle furnace ok
Installed new humidifier aprilaire 600 thermostat is controlling humidity test and check for water leaks no leaks found humidifier is set to 37% level in thermostat. Removed current flex line from inside heater cabinet and replace it with hard pipe all the way to heater gas shut off valve used 12 inches of track pipe, leak check all fittings and connections that were made in todayâ€™s visit and they all Are leak free,
Performed PECO Check, checked air filter ok. Checked voltage, amperage and electrical connections. Tested electric back up heaters. Found breaker and wire undersized for electric heaters. Found 8 wire and a 40 amp breaker on a 10 kw heater. Recommend upgrading wire and breaker to 60 amp breaker and 6 wire. Cleaned condensate trap. Started heat pump, checked refrigerant charge. Tested defrost cycle. Calculated btu output. Checked operation and temperature rise across coil.
Performed precision heat tune up on thermopride oil furnace. Aprilaire 501 filter is ok. Replaced.65 60a nozzle. Garbar oil filter ok. Checked combustion and performed a smoke test. Serviced humidifier with #35 pad. Oil furnace is working fine at time of service.
Performed heating maintenance, replaced standard air filter. Checked burners and flame sensor, inspected heat exchanger. Blew out condensate trap. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started gas furnace, tested limit and safety switches, measured fuel pressures and performed combustion test. Checked operation and temperature rise.
Checked no cooling blower not ramping up to speed. Checked blower motor, found motor will run on low speed but will not ramp up. Motor not responding to high speed call. Jumped out low and high to ramp blower. Tested motor, now ramps up to high speed.Did not email
Performed Precision Heating Tune Up on System. Filter is in good condition at this time. Recommended to homeowner to check filter after the Heat is being used and replace as needed. Cleaned and Serviced Humidifier. Tested Humidifier and set Humidistat Control to 35% for the Heating season. While inspecting Electrical Components, found Blower Capacitor testing very low. Installed new Capacitor and tested operation. Performed Combustion Analysis on Furnace. Furnace Age is about 14 Years old. Average life of a Gas Furnace is around 15 years. Due to age, would recommend begin saving for replacement of the Gas Furnace/AC system.Spoke with Homeowner about Water Heater and have included an estimate for the Replacement of the Water Heater.
Performed oil cleaning on furnace, check electrical low and high ok replace filter, clean heat exchanger and flue pipe, also replace nozzle and clean/adjust electrodes ok replace oil filter, performed smoke test and combustion test , overall condition is poor, burner is burning very poor not burning correctly 100% tried to adjust as much as possible so unit does not burn incorrectly.....unit should get replace due to age/condition and for safety purposes
Performed two propane gas furnaces check ups, checked electrical low and high ok both filters ok clean flame sensor and check burners ok combustion test and cycle heaters ok check supply temp and return temp ok noticed no humidifier for first floor would recommend installing a humidifier to prevent dryness in the winter months
Performed heat pump check up heat side, check electrical low and high ok 10 kw back heat ok, coil is clean also replace high efficiency filter, check split ok outdoor unit pressures ok r22 check caps and contactor ok test reversing valve ok outdoor temp 79 413
Performed oil boiler cleaning check electrical low and high ok clean heat exchanger and flue pipe, also clean chimney base, replace nozzle and readjust electrodes, adjust air ratio and check for smoke ok no smoke combustion test ok check all 4 zones ok, water pressure and temp ok replace connector on board due to moisture inside and made it short cycle boiler ok
Drained and removed old water heater. Installed new water heater in pan on bricks. Reconnected copper lines and replaced valve and expansion tank. Insulated hot pipe. Reconnected electric. Installed new big goose water alarm in pan. Checked thermostats and tested water temperature.
Performed gas heat inspection check electrical low and high ok filter ok check pilot tube and 24 volts smart valve, ok gas pressure ok check blower ok, performed combustion test, also check integrity of heat exchanger, visual inspection look in bad shape heavy rust areas everywhere, and check combustion with blower on and off there was 2 percent change grater with blower on, due to results of testing would recommend replacing furnace before problem gets extreme, and un safe to use furnace,
Checked boiler vent leak. Checked ss venting, tighten all clamps. Checked termination ok. Cleaned burners and flame sensor. Inspected heat exchanger. Checked voltage, amperage and electrical connections. Started boiler, checked vent leaks, found no leaks. Performed combustion test, checked boiler pressure and temperature. Measured fuel pressures ok. Checked operation.
Removed old trunk and plenum re ran new supply trunk out of metal duct and metal plenum instead of duct board old plenum and duct board trunk covered in mold and emitting fumes from duct. Installed reme halo and the smells gone. Recommended thermostat with circulation option for reme performance. Also checked multiple units same issue with mold and dirt in ducts.
Performed heating maintenance, cleaned burners and pilot burner, inspected heat exchanger. Checked voltage, amperage and electrical connections. Cycled boiler thru first floor thermostat, measured fuel pressures. Performed combustion test. Checked boiler pressure and temperature.
Performed gas heat tune up check electrical low And high ok clean sensor check gas pressures ok combustion test replace customer supplied filter, informed customer about humidifier replacement or repairing with new tray and new kit, recommended new humidifier, also informed customer about flex pipe inside heater cabinet, by code only hard pipe should be used, emailed pricing for repairs,
Performed Quality Assurance On Amana AC/Coil installation. Reviewed installation and completed Checklist Form in System. Replaced Air Filter on System. Inspected Wiring on thermostat and at Control Board. Homeowner stated that after we installed the AC the Heat came on one time, but hasnâ€™t had any issues since. No issues with the Wiring found. They have a NEST thermostat installed. Cycled AC multiple times and System was turning on/off properly.