DiBiase Heating & Cooling Company provides air conditioning, heating and water heater services to our neighbors in the Merion Station, PA areas. Since we opened our doors in 2008 we have lived by a code of integrity, honesty and quality.
Your complete comfort is our #1 priority. Read our reviews and find out why your neighbors consider us to be their local partner for quality heating, air conditioning and water heater services in Merion Station, PA.
for Merion Station, PA
Our Reviews by City
Frank - Merion Station, PA
pleasant and professional
Service call that the Air Conditioner was not Cooling properly. Arrived onsite and spoke with Homeowner about issue. Found the Indoor Coil was completely frozen solid and the Drain Line was blocked due to the Coil being frozen causing the water to over Flow out of the Unit into the Auxilary Pan. Drained the Water and defrosted the Indoor Coil. On previous visit, we added Refrigerant to the system and Leak Dye. Used UV Light to examine the Indoor a Coil. Large amounts of Dye were present throughout the entire Indoor Coil, indicating that the Indoor Coil has a Refrigeramt Leak. Turned System back on and measured Refrigerant Charge. System was low on Refrigerant causing the Indoor Coil Temperature to be below the Freezing mark. Added 3lbs of 410-A Refrigerant to system, charging by Subcooling.We will follow up with options for Repair/Replacement of the Indoor Coil/AC System.Also recommend installing an EZ Trap and Wet Switch into the system. If the Wet Switch detects Water in the Au
Found unit scooted up on arrival. Removed covers and brushed and vacuumed heat exchanger, chamber, and chimney ey base. Replaced oil nozzle with 1.25 80B nozzle. Fired and tested unit and adjusted combustion. The combustion chamber liner is falling apart. Recommend boiler and oil tank be replaced.
Performed Precision Air Conditioning Tune Up on system. Replaced the 201 High Efficiency Air Filter. While testing the electrical components found the Blower Capacitor was testing below Rating. Replaced the Blower Capacitor and tested operation. While measuring Refrigerant Charge found Superheat to be high and Subcooling Levels were low. Added 2lbs of 410-A Refrigerant to system to raise Subcooling to proper levels. Added Leak Dye to the system. Due to the system needing refirgerant Charge and adding the Leak Dye to the system, the homeowner would like us to come back out in the next 30-45 Days to inspect the system for the leak. The office will contact to schedule the leak search.The office will follow up for payment due to the homeowner not being home at the time of service.
Upon arrival found unit running to manufacture specifications. No noise . Unit is functioning properly.Relief valve is leaking and needs replaced.