When you need air conditioning, heating and water heater services in Ogden, PA, you need DiBiase Heating & Cooling Company. We’ve earned a reputation over the years for providing customer-first service you can count on.
We live by rock-solid values of integrity, honesty and quality. Read our reviews and find out why your neighbors think of our trusty frog mascot whenever they need local heating, air conditioning and water heater services in Ogden, PA.
for Ogden, PA
Our Reviews by City
Service call to inspect the Duct-Work for the Oil Furnace/AC system. Homeowner recently purchased the House and is having trouble with the Air Flow in the Bedroom. Inspected the Ductwork which is in poor condition. Viewed multiple areas where the Take Offs are not properly sealed and on at least one run the Take Off is not connected. A Duct Fan Booster had been previously installed on the Supply Duct for the Bedroom. The Main Supply Trunk Line is 16" x 8" and the Main Return Trunk Line 12" x 8". The Bedroom Supply run is a 10" x 3" Trunk Line that transitions to 8" Flex Duct to accommodate the Booster Fan. The Flex Duct for the Supply of the Bedroom is tied in at the end of the 10" x 3" Duct Run. The Bedroom is also located above a crawl space that has very minimal insulation. Total Square footage of House is 1450 Sq. Ft. Bedroom size is about 11' x 15'.We will follow up with an estimate to repair Duct Work that is not connected properly. We will look at the Duct Sizing and design,