DiBiase Heating & Cooling is the top-rated HVAC service according to the residents of Parkesburg, PA and the surrounding areas. Find out why so many people love their service experience with DiBiase.
An HVAC tune up will run you about $100 - $200 per visit, on average. There are two visits a year- one for the air conditioner and one for the heating unit. The price of the tune up has been proven to be well worth the cost when considering the benefits, which include:
- The unit will run better and lower energy consumption, helping with your power bills.
- A tune up will help prevent unexpected pricy future repairs.
- Regular maintenance extends the life of your HVAC so you won’t have to think about the expense of a replacement for a while to come.
The average price Parkesburg, PA residents can expect to pay for an HVAC repair is $300. Small repairs will generally run from $75 - $250, while larger HVAC repairs could cost up to $3,000. What is wrong with the HVAC will directly impact what the repair will cost.
Are you having issues with your HVAC? DiBiase Heating & Cooling is happy to help. Request an estimate today for repair service and one of our highly trained technicians will be in touch promptly.
It will cost between $700 - $2,100 to replace an evaporator coil on your HVAC system, including parts and labor. An evaporator coil works by collecting heat from your home as the refrigerant in the system evaporates from a liquid to a gas. That warm air is transported outside and you are left with cool inside air. Without a properly working evaporator coil your HVAC will not function to cool your home.
Reviews give us a sense of a company's personality before you call. Check out what your neighbors are saying and find out why all the towns nearby consider us to be their nearby heating and air company in Parkesburg, PA.
for Parkesburg, PA
Our Reviews by City
Luis always does a great job..
Tim - Parkesburg, PA
Luis always does a great job, is on time and is always very helpful.
Awesome service, as usual!
Alexis - Parkesburg, PA
Awesome service and always there when you need them!
Alexis - Parkesburg, PA
Five years ago, I never heard of this company, my heater died on the coldest day of the year and I called everyone that I had seen advertised on TV and no one would come out. Someone gave me this name and they were here in a heartbeat. Same thing happened with my AC going out on the hottest day this year, and guess who was here in a minute. Really, when you're freezing or too hot to even think and your system has a problem, there is nothing more important than knowing someone will be here to help. That is this company!
Always pleased with the service from this company!
Alexis - Parkesburg, PA
Matthew - Parkesburg, PA
Matthew - Parkesburg, PA
Luis was great. Thanks for sending him
Great Service and pleased
Tim - Parkesburg, PA
Service Technician was on time, very nice, professional and completed work required. Very pleased.
Tim - Parkesburg, PA
Pleased with technicians work and he is a nice guy
Professional as always
Blacklotus2021 - Parkesburg, PA
Service was great, on time and Luis is very helpful and professional.
Tim - Parkesburg, PA
Service was great, on time and Luis is very helpful and professional.👍
Warren - Parkesburg, PA
Had a lot of great tips!
Lori - Parkesburg, PA
Knew what he was doing and had a lot of great info to share.
arrived earlier than expected and did a great job
Sumu - Parkesburg, PA
Repaired manual damper for second floor, after repairs check and adjust air flow, now all registers are getting good flor, went over thermostat settings with customer and recommended setting fan to on, also went over scheduling and how to switch priority between sensor and thermostat, cycle unit ok check supply and return air ok 70/51. No charge for todayâ€™s visit
Performed Precision Air Conditioning Tune Up on Heat Pump System. Replaced 16x20x1 Air Filter. Cleaned Drain Line and Condensation Pump. Inspected Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge on system. System is running to standards.
No ac, talked to tenant upon arrival they explained me that the ac was working normal, on Monday they set the thermostat to 68 and ran all day, room temp was 73 never reached 68,,,,A/C system is working properly will be very hard to reach 68 degrees, design temperature is 74
Performed quality assurance on recently installed unit, did not passed inspection...unit has not work properly since installation, found system low on refrigerant, repaired leak at liquid line after repairing leak, evacuated Down to 350 microns, added 3 lbs of refrigerant system pressures are within manufacture specifications 275/140 with 5 sub cooling and 10 super heat, supply air 60 F return air 78F system is set up for 1045 cfm check airflow Throughout the house vents good flow coming out of all vents, cycle unit system is cooling great.
Performed ac tune up check electrical low and high ok replace filter check split flushed drain, ok check outdoor unit refrigerant pressures r22 ok capacitor ok noticed contactor has burnt marks on contacts also super boost Getting hot when unit is running informed customer about system condition, customer will wait until breaks completely
Performed ac tune on heat pump and Straight ac check electrical low and high ok replace filters, check and flushed drain test pump ok check split blowers ok check outdoor units refrigerant pressures r22 and 410 ok both units are working ok older unit is working little harder cycle both units ok
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip and Amana condenser. Flushed lineset. Brazed in lineset with nitrogen. Installed new drip pan and unico high velocity system. Wired in control module and attached the 2 halves. Connected supply and insulated. Installed new ez trap and wet switch and wired to break r. Reattached condensate drain. Brazed in lineset with nitrogen and pressure tested to 300 psi then evacuated down to 167 microns. Wired in electric strip heater and tested. Tested in cooling and adjusted charge. System working great at time of install.
Business owner informed me that making a call for cooling at stat actually caused increase in room temperature. Made call for cooling. System ran in heat mode. Checked installer set up for proper reversing valve set up; ok. Found 18-5 wire at outdoor unit torn (reversing valve conductor severed). Called Harry to approve pricing/repair (diagnostic/low voltage wiring repair) rewired low voltage and secured in several spots. Tested system in cooling mode. 23F temp rise; ok.
Performed precision a/c tune up on 2005 Rheem a/c. 16x24x1 air filter was just replaced. Checked all electrical conections and components. Blew out condensate drain. Checked temperature split, found I was only getting a 14 degrees temperature split. Found system low on charge. Explained to homeowner that it is an r-22 System and both the furnace and a/c system should be replaced. Set up appointment with office to have a comfort consultant come and give a quote on replacement. A/c system is not working well at time of inspection.
Removed existing furnace and air conditioner. Installed new Amana furnace and air conditioner. Moved new outdoor unit to customer specifications. Flushed existing line set and made all necessary connections. Installed new disconnect and whip. Pressure tested and vaccumed down to 390. Added 6 ounces of refrigerant, cracked valves. Adapted to existing return. Built new supply plenum and sealed plenum. Installed new t-10 thermostat and went over with customer. Installed new condensate pump and moved discharge to sewer. Installed new ez trap. Adapted to existing gas and flue piping. Tested system in heating and air and went over install with customer. Cleaned work area.
Found that thermostat that was replaced last November has failed. Found that when thermostat was in cooling mode on the thermostat it was not picking up the o terminal to energize the reversing valve for cooling mode. Replaced Honeywell t-4 thermostat with Honeywell t-6 thermostat. Tested system in cooling mode. Heat pump is working fine at time of service. Honeywell thermostat is a warranty thermostat. Waived diagnostic fee.
Performed AC tuneup on a 2003 ICP unit checked electrical low and high voltage connections replace air filter flush condensate test pump checked supply return temperature found to be only 10Â° differential check blower cap reading below standard check outdoor unit refrigerant r22 capacitor and contactor, contra making noise and has black marks on contacts, capacitor is reading within range, unit is low on refrigerant indoor coil is very rusty mostly likely indoor coil is leaking informed customer about condition of HVAC UNIT and provided options
Performed quality assurance on daikin mini split heat pump. Found electric fead not sealed. Siliconed around electric. Checked temperature split and rise in heating and cooling. Checked electrical conections. Made sure homeowner understands how to use the remote. System is working fine at time of service.
Installed new Daikin mini split. Head unit mounted inside kitchen towards hallway. Installed new line set and line hide. Installed outdoor unit on stone and leveled pad. Installed new wire and 30 amp breaker to supply power for outdoor unit/head unit. Completed all connections with flare tite fittings and torqued to manufacturers specifications. Completed all wiring for head unit and outdoor heat pump. Unit tested in heating and cooling and is working properly.
Upon arrival found thermostat calling for heat but no flame or blower running, inducer running making high pitched sound, furnace is not working properly, after performing furnace inspection found that unit keeps going off on high limit, blower not coming on, found mother board relay not closing to bring blower, check blower operation and works ok, at this time could not performed tune up due to the furnace needing some parts, explained situation to Harry and quoted for repair customer ok repsirs and paid 50% office will get back to customer regards rerun call with new parts and come back to finished up tune up installed new inducer and fan timer also new thermostat cycle and test furnace ok also performed heat tune up, cleaned flame sensor, check manifold propane pressure ok performed combustion test ok replaced air filter, check supply and return temp ok cycle furnace ok,
Performed oil furnace tune up cleaning, cleaned heat exchanger and flue pipe, flue pipe needs to be changed, also replace oil filter and nozzle, noticed nozzle sized was .75x70B furnace is rated at 1.00x70B replaced nozzle with 1.70 but when system was put in test after cleaning, found to running in rough conditions so replace nozzle to .75x70B, also electrodes are in bad shape flat ends, could not replaced pump strainer could not stop the flow of oil, customer has underground tank and thinks is pretty full, so level could be higher than burner no other way is stoping flow, performed smoke and combustion test, noticed high co numbers, adjust air to fuel mixture, left side of heat exchanger levels are ok good CO2, oxygen, and CO OK, but I right side co levels go higher, performed smoke test and failed test, base on manufacture technical support, heat exchanger has failed and repairs and replacement should be done, turned electrical switch off to furnace, explained to customer about heat
Customer has oil furnace from 1987, customer stated that blower does not stops, check oil furnace operation, cycle couple times and fan did cycle off based on temp limit switch, did noticed burner chamber has two big cracks and front end is broken, also found electrodes almost flat at the ends, performed combustion test cycle furnace, blower motor and main pulley is making grinding noise, due to overall condition system should be replaced office will follow up tomorrow morning to schedule consultation of new havac system
Found oil furnace not firing. Oil tank was just filled. Thought at first that the nozzle was clogged but pulled it out and it was ok. Found transformer spark was ok but not that great. Recommend we replace the transformer. Replaced the transformer and made sure electrode gapping was correct. Furnace fired right up . There was a lot of un burned oil in the chamber , burned off and checked combustion readings. Oil furnace is working fine again at time of service.
Replaced blower motor, blower relay, motor wiring harness , and t-4 thermostat. Cycled on heat pump system in heating mode. Outdoor ambient air temperature is 46 degrees. 410a refrigerant pressures in heating mode are 291/103. Checked temperature rise in heating mode and it was exactly 20 degrees. Had Eric from hvac check over everything. We jumped out the indoor fan motor at wiring strip from rot g terminals and r to w terminals. Heat pump is cycling on and of correctly at time of service.
Performed heat pump tune and also oil furnace cleaning, check electrical low and high ok replaced both filters, check back up heat on heat pump, temp rise outdoor unit refrigerant pressures ok test defrost ok cycle heat pump ok. On oil furnace cleaned flue pipe heat exchanger and replace nozzle, oil filter, performed smoke and combustion test unit is working at the time of service cycle both units ok
Replaced blower relay with newer style relay. Call tech support to let them know the procedure that is being taken. Checked electrical conections on new core sense. Cycled heat pump threw emergency heat, heat pump heating, and cooling mode. Blower is coming on at the appropriate times. Let homeowner know that we are going through the steps to find out what is causing these lock outs to occur and to keep us informed if any new situation occurs.
Performed oil furnace tune up cleaning, clean heat exchanger through exchanger clean ports, and tried to clean as much as possible from rear flue. Very hard to removed flue, replace nozzle pump strainer and oil filter, performed smoke and combustion test ok check temp rise supply 120 rerun 73 cycle furnace ok
Customers thermostat has lost power, check 24 volts on air handler and at thermostat found 24 volts preset, check electric back up heat ok check outdoor unit and found burnt components on the outside heat pump, took photos os condition recommend replacing heat pump we will come out tomorrow to provide options to customer
After talking to homeowner about issue, he had mentioned that about 2 nights ago he had noticed the outdoor heat pump running, but not the fan at the indoor blower. Put gauges on system and got homeowner to give a call for heating. Called tech support and gave them model and serial numbers of indoor and outdoor heat pump. Had pressures ind heating mode at 68 degrees of 326/123. He wanted me to check the super heat in heating mode and verify static pressure. Static pressure was .5 w.c. . And had a super heat after 15 minutes of run time of 9.8. He had mentioned that possibly the ice cube relay inside the air handler was not picking up the fan, but homeowner said he had no issues in cooling mode. Told Phillip to keep any eye on it and give us feed back if he notices outdoor unit running with out the indoor blower,
No ac found outdoor unit locked out on code 2 compressor issues, check capacitor ok fan motor or ok reset unit and ran on heat and cool mode test defrost ok refrigerant pressures ok, air filter ok blower motor ok, would recommend a maintenance visit some time this fall or winter to double check unit, core sensor might have internally failed and may need to be replaced if same issues occurs