When it comes to your Upper Darby, PA’s home heating, cooling and water heater systems, DiBiase Heating & Cooling Company makes sure they’re running at peak efficiency for your improved indoor comfort, convenience and safety.
This is a service promise and a reflection of our core values: integrity, honesty, quality. Read reviews from your neighbors in Upper Darby, PA to see how we live up to these values every day, in every way.
for Upper Darby, PA
Our Reviews by City
Performed Precision Heating Tune Up on Gas Fired Boiler. Removed Burners and Ignition Assembly. Cleaned Burners and Ignition Assembly. Inspected Heat Exchanger which is clear but is very rusted. Burners and Burner area are rusted as well. Put system in operation and performed Combustion Analysis on Boiler. Combustion Results were all within standards. Tested Expansion Tank for Air Pressure. While the system was running the Gas Valve Soleniod began opening/closing multiple times. The 24 Volts to the Main Valve at the Ignition Control was quickly dropping in/out. Before I could verify the cause of the issue it stopped. Ensured all connections were tight and monitored the Boilers operation. The system was working with no issues. Spoke with Homeowner about issue as it was occurring. If this begins to happen again we will have to further troubleshoot the cause of the issue.